# Proper connections after solar charger

HandymanJoe
Registered Users Posts:

**3**✭
I have 4-100 watt panels wired in parallel to the charge controller, then to the battery bank with connections made. Now where do i connect the heavy wires to the inverter.

## Comments

32,027adminHere is a quick explination of how to configure a battery bank with two or more parallel strings of batteries:

http://www.smartgauge.co.uk/batt_con.html

From the charge controller to the battery bank, you want the cables (and fuse/circuit breaker) to be (ideally) 1.25x larger than the expected maximum current:

- 400 Watts of panels * 1/17.5 volts Vmp array = ~23 Amps expected maximum continous current
- FYI: 400 Watts * 0.77 typical best case current * 1/14.5 volts charging = 21 amps typical best case harvest current
- 23 Amps * 1.25 NEC derating for continuous current = 29 Amps ~ 30 Amp minimum controller to battery bank branch circuit wiring/breaker/fuse ratings.

You also want a maximum voltage drop of ~0.05 to 0.10 volts (12 volt bank) from charge controller to battery bank with ~21-23 amps (low voltage drop, faster/more accurate charging--Charge controller "sees accurate" battery bank voltage).Typically the heavy current cables are from the battery bank to common +/- connections. The AC inverter typically draws the most current.

Say you have a 400 Watt AC inverter, the maximum current would be:

- 400 Watts * 1/0.85 inverter AC efficiency * 1/10.5 volt battery cutoff = 44.8 Amps

Note that most AC inverters will source ~2x more AC power (i.e., 400 Watts * 2 = 800 Watt) surge power (starting AC motor, etc.).Recommend a maximum of 0.5 volts from (12 volt) battery bank to DC input of AC inverter at maximum inverter power.

The simplified NEC (national electric code) cable ratings are:

https://lugsdirect.com/WireCurrentAmpacitiesNEC-Table-301-16.htm

When dealing with solar/electrical--Details matter here... Charging/discharging current. Battery bank AH and Voltage rating (type of batteries too). Length of wiring/cabling, etc.

Fuses and Circuit Breakers are there to prevent your wiring from overheating/catching/setting fires. For "unattended" solar system operation (nobody present), you want to ensure that you are protected against fires/etc.

Many times, fuses are nice because they do not only protect against over current... They give you handy on/off switches too (and many times, breakers are the same price or cheaper than fuses--Especially at higher current ratings).

-Bill

5,658✭✭✭✭✭- Assorted other systems, pieces and to many panels in the closet to not do more projects.

3✭32,027adminFor a 12 volt battery bank, for accurate/fastest charging, you want aroun 0.10 to 0.20 volt drop so that charge controller "sees" accurate charging voltage... Just some quick math:

- 400 Watt array * 0.77 panel+controller derating * 11/4.5 volts charging = 21.2 volts (more or less) best case charging current

If you use a simple voltage drop calculator like this one, 10 AWG cable, 14.5 volts charging, 21.2 amps charging current and 2 feet for # 10 cable from charge controller to battery bank (one way cable run for this calculator):https://www.calculator.net/voltage-drop-calculator.html?necmaterial=copper&necwiresize=2&necconduit=pvc&necpf=1&material=copper&wiresize=0.4066&resistance=1.2&resistanceunit=okm&voltage=14.5&phase=dc&noofconductor=1&distance=2&distanceunit=feet&eres=21.2&x=59&y=21&ctype=nec

## Result

Voltage drop:

Ideally, 2 feet or less wire run for 0.10 volt drop--Or heavier cable to have less voltage drop.0.10Voltage drop percentage:

0.70%Voltage at the end:

14.4Having 0.2 volt drop is not the end of the world... But you can see that running relatively small 10 AWG cable does severely limit cable run from charger to battery bank.

Following the Inverter installation instructions is always a good start... If you can tell us a bit more about your system (type of battery bank, AC inverter Watt rating, length of cable from battery bank to inverter, etc... We can help a bit more.

Having an AC inverter with a "real" on/off switch of some sort is a big help (turn off when not running AC loads can save "tare losses" from an idle inverter with zero loads)... And if no true on/off function, then a circuit breaker from battery to AC inverter DC terminal is nice.

-Bill

3✭32,027adminIt is best if you make your Q&A's here in the forum... We really are not setup to have "wall" discussions as most people do not look/follow them:

There can be other issues too..

- Check the DC input voltage... Low DC input can cause low AC inverter output
- Is your Dremel tool not working? (running slow, not starting/buzzing?)

Not knowing what brand/model of AC inverter is kind of a issue--Dont know if PSW or MSW type... PSW/TSW (Pure/True Sine Wave) inverters have an output that is near identical to what you get from utility power.If this was an MSW (Modified Sine/Square Wave) inverter--There are other issues. MSW inverters will typically read "low" output voltage when using a typical DC voltmeter.

If you have an RMS (Root Mean Square) AC volt meter, they will read lower voltage for an MSW (modified square wave) inverter. RMS or Root Mean Square reading meter--It takes multiple samples of an "arbitrary" wave form (sine wave, square wave, modified square wave) and "integrates" the area under the wave form and gives a voltage that is the equivalent "power" of a DC voltage.

True RMS meters used to be much more expensive, and rarely seen (see Fluke)... Newer meters even down to the $50 level are available these days.

https://www.fluke.com/en-us/learn/blog/electrical/what-is-true-rms

A typical non-RMS reading digital meter simply reads the peak voltage of the sine wave and divides by the square root of 2 to get the RMS equivalent:

- 120 VAC * srt(s) = 170 Volts peak

https://electricalacademia.com/renewable-energy/inverter-types-working-principle-sine-wave-square-wave-modified-sine-wave-inverter-working/If you connect other loads (lights, drill, etc.) to the inverter, do the other types of loads work at all?

At this point--I am not ready to blame the 108 VAC reading on the inverter as causing your Dremel tool problems.

There are some AC loads that have problems with MSW inverters. The MSW wave form has a "lower peak voltage" than the PSW type. And some power supplies have problems with that lower voltage--Looks like an "AC brownout" condition.

Another issue is that MSW wave forms have lots of "harmonics" (PSW ~ 5% or less total harmonic distortion and MSW have something like 25-30% THD). For transformers, induction motors, and some other AC power devices have problems with the high THD and they can overheat and fail (quickly or over time). Instead of less than 5% THD being converted to heat, and MSW inverter can have 25-30% THD converted to heat (in transformers, induction motors, and such).

There are also (mainly older these days?) tool battery chargers that failed on MSW inverters...

Not to say that all will fail on MSW--Probably 80% of AC loads work fine, and 10-20% can overheat/fail. If you plug in battery chargers and other small electronics & wall transformers, watch their temperature and unplug if they are overheating. And don't use an MSW inverter to power induction motors--Especially those used for refrigerators and freezers (these are "heavily loaded compressor induction motors and are known to "run hot" on MSW).

-Bill