Off Grid Solar & Battery Systems
charging battery bank with generator
Do you have the inverter hooked up to a panel wired split phase and use any 240v loads? Or are your loads 120V, trying to get a picture of what it is you have, a solution such as
suggested using a smaller inverter during periods of low demand, at night for example would dramatically reduce the taxing of the batteries by shifting the 24 hour loads to it. How are you determining the DOD of the battery? Again, just curious.
1500W, 6× Schutten 250W Poly panels , Schneider MPPT 60 150 CC, Schneider SW 2524 inverter, 400Ah LFP 24V nominal battery bank
900W 3 × 300W No name brand Poly panels, Morningstar TS 60 PWM controller, no name 2000W inverter 400Ah FLA 24V nominal as a backup system.
5Kw Yanmar clone single cylinder air cooled diesel generator for rare emergencies and welding.