# Isaias is coming my way

mountainman
Registered Users Posts:

**378**✭✭
Lately Heat index here in nc has been 106.

my SO has breathing issues so ac is a necessity

Last hurricane sept 19 power was out for 2 weeks.

I was calculating what i could run with my 1700 2000 surge genny.

My 115 volt 10000 btu window unit list 8 amps and 825 watts?

I'm confused shouldn't 8 amps x 115 v be 920 watts?

My chest freezer 200 watts running.

50 watts 40" tv for weather updates

100 watt box fan on high speed

24 watts for 2 12 watt led lamps

11 watts for 2 5volt 2.1 amp phone chargers

385 watts plus ac 850 or 920

Say 1300 watts worst case 77%

Of 1700 watt generator rating..

Does this sound doable thought anyone?

my SO has breathing issues so ac is a necessity

Last hurricane sept 19 power was out for 2 weeks.

I was calculating what i could run with my 1700 2000 surge genny.

My 115 volt 10000 btu window unit list 8 amps and 825 watts?

I'm confused shouldn't 8 amps x 115 v be 920 watts?

My chest freezer 200 watts running.

50 watts 40" tv for weather updates

100 watt box fan on high speed

24 watts for 2 12 watt led lamps

11 watts for 2 5volt 2.1 amp phone chargers

385 watts plus ac 850 or 920

Say 1300 watts worst case 77%

Of 1700 watt generator rating..

Does this sound doable thought anyone?

Blue ridge mts. Renogy pwm 4 100 watt and 2 190 evergreen on Epever mppt 30. 4 Gc 208 ah @12 volts 300 watt psw inverter. 2 kw genny. Iota 45.

#### Categories

- 25.9K All Categories
- 199 Forum & Website
- 107 Solar Forum News and Announcements
- 1.3K Solar News, Reviews, & Product Announcements
- 150 Solar Information links & sources, event announcements
- 855 Solar Product Reviews & Opinions
- 246 Solar Skeptics, Hype, & Scams Corner
- 20.5K Solar Electric Power, Wind Power & Balance of System
- 3.3K General Solar Power Topics
- 6.2K Solar Beginners Corner
- 920 PV Installers Forum - NEC, Wiring, Installation
- 1.9K Advanced Solar Electric Technical Forum
- 4.8K Off Grid Solar & Battery Systems
- 350 Caravan, Recreational Vehicle, and Marine Power Systems
- 979 Grid Tie and Grid Interactive Systems
- 598 Solar Water Pumping
- 777 Wind Power Generation
- 611 Energy Use & Conservation
- 460 Discussion Forums/Café
- 214 In the Weeds--Member's Choice
- 71 Construction
- 91 New Battery Technologies
- 84 Old Battery Tech Discussions
- 3.8K Solar News - Automatic Feed
- 3.8K Solar Energy News RSS Feed

## Comments

792✭✭✭✭378✭✭What's the deal with the ac amps vs wattage?

30,721adminUse a rope between two cars. If you have the two cars in line, and pull 500 lbs on the rope with the first car, the second car will also see 500 lbs pulling it forward too...

Second example is to have the first car 60 degrees off to the side of the first car (pulling rope at 60 degree angle). Cosine of 60 degrees is 0.5 or 1/2 of the force of the first car is applied to the second car pulling forward. If you still want to pull the first car forward with 500 lbs, you would need to put put 1,000 lbs of force on the rope to pull forward (the rope needs to be 2x stronger to do the same amount of "work").

Similar with AC power... You have a 60 Hz voltage sine wave. If the load is a resistor--The current will follow the sine wave exactly in phase. Cosine of zero degrees is

If you are, for example, driving an induction motor, the current will typically "lag" the voltage by some amount. That is the "cosine" of the phase angle between the voltage and the current. That Cosine of XX degrees we also call the "power factor".

A typical induction motor may have a PF somewhere between 0.65 to 0.80 or so... The math looks like:

- Power = Voltage * Current * Power Factor

That is the power/energy that is needed to "do the work" (i.e., power from battery, generator fuel, etc.). However, the wiring, transformer, generator/alternator/AC inverter needs to be "heavy enough" to move the "extra current" because of the Power Factor issue. We can use Voltage*Current or VA to represent the sizing of wiring/fuses/etc. to carry that "extra current".- VA = Voltage * Current

The name plate ratings of many appliances are difficult to use in accurately predicting performance/energy requirements. Sometimes they are "worst case" numbers--Other times, they seem to be "nominal" or average numbers. And the name plate rating almost never takes into account "surge current" (induction motors can take upwards of 5x running current for starting current).Take the 8 amp @ 115 VAC A/C unit and 825 Watts:

- VA = 8 amps * 115 VAC = 920 VA
- Power = VA * Power Factor: PF = Power / VA = 825 Watts / 920 VA = 0.90 Power Factor

So, in this case, the wiring has to be 1/0.90 heavier because of the PF (1.11 x heavier wiring/AC inverter/Genset/etc.).0.90 PF is not bad... Typically anything >=0.95 PF is considered pretty much "perfect PF" (1.0 is perfect).

There are things the manufacture can do to make for better PF... For example, they can put a properly sized capacitor in parallel with the motor and "correct" the power factor to ~0.95 (for other reasons, correcting to 1.0 PF can cause major issues with induction motors and capacitors).

Or the Mfg. can put an "inverter" between the input main power, and the motor/load. The input of the inverter is near 1.0 PF, and the inverter does what is required to run the motor (i.e., motor PF is not "seen" on the inverter's input connection).

https://en.wikipedia.org/wiki/Power_factor

This is not simple stuff... And separated Tesla from Edison (Tesla the math genius, and Edison the practical physical researcher):

https://en.wikipedia.org/wiki/War_of_the_currents

Using a Kill-a-Watt type meter which can measure Volts, Amps, Power Factor, Watts and kWatt*Hours can give you a pretty good estimate of what is happening on your power cord (estimate, still an inexpensive instrument doing the measurements, not a lab grade measurement system).

https://www.amazon.com/s?k=kill-a-watt+meter

So, for our needs... Use Watts to estimate battery power (rate of energy use: Watts) and energy usage (amount of energy used: Watt*Hours). And use VA to size the AC wiring/AC inverter/genset/etc.

Note: There are different types of meters out there... There are the "cheap" meters which make assumptions (like Sine wave AC voltage and amperage wave forms), and others that have more powerful chip set which can measure "arbitrary" wave forms (sine, square, pulses, etc.)... They are called "True RMS" reading meters.

https://www.fluke.com/en-us/learn/blog/electrical/what-is-true-rms

A standard meter only measures the "average" voltage or current waveform and applies a conversion factor for Sine Waves (i.e., Peak Voltage * 1/1.414 (or sqrt of 2)) to convert peak sinewave voltage to the "true RMS" value of the voltage:

- 120 VAC * 1.414 conversion = 170 Volts sine wave peak

Or, work wise (Watts, Watt*Hours) a 170 Volts peak sine wave does the "same amount of work" as a 120 Volt DC power source when driving a resistance heater.A True RMS meter will "sample' the wave form something like 50,000 times a second (for a meter used on 60 Hz power lines) and "do the math" to estimate the true RMS value of the signal (RMS=Root Mean Square==Basically the "average power" under the wave form==I.e., Power=V^2/R -- That is why "square root" average, and not regular averaging).

-Bill

5,278✭✭✭✭✭https://www.amazon.com/dp/B08677DCKN/ref=sspa_dk_detail_0?psc=1&pd_rd_i=B08677DCKN&pd_rd_w=xu9Dq&pf_rd_p=48d372c1-f7e1-4b8b-9d02-4bd86f5158c5&pd_rd_wg=ybdMB&pf_rd_r=4F63KJTDBTGHMWW7XDV7&pd_rd_r=dfddcf2f-8eea-407f-a00e-9da0d03e0294&spLa=ZW5jcnlwdGVkUXVhbGlmaWVyPUFQT1RFMU9RSjRaT1kmZW5jcnlwdGVkSWQ9QTA0OTMzOTEyWFBSTEk0U01EU1omZW5jcnlwdGVkQWRJZD1BMTA0MzkwNjFLUTMyUzhaWTlTRE0md2lkZ2V0TmFtZT1zcF9kZXRhaWwmYWN0aW9uPWNsaWNrUmVkaXJlY3QmZG9Ob3RMb2dDbGljaz10cnVl

http://members.sti.net/offgridsolar/

E-mail [email protected]

8,864✭✭✭✭✭For general house loads, I'd stick with old fashion alternator gensets, and skip the inverter generators, you don't need super clean power for an air conditiooner.

|| Midnight Classic 200 | 10, Evergreen 200w in a 160VOC array ||

|| VEC1093 12V Charger | Maha C401 aa/aaa Charger | SureSine | Sunsaver MPPT 15A

solar: http://tinyurl.com/LMR-Solar

gen: http://tinyurl.com/LMR-Lister ,

1,292✭✭✭I took my 240v 48k btu central air from 200 amp startup surge to 73 amps. Run current is 14 amps. I run it on two old SW5048+ units that have the needed surge capabiliity.

378✭✭And the power is out.

1700 watt old style genny running 10 btu ac a box fan and a couple 12 watt led lamps. It sounds like its loaded.

Come day light I'll see how much damage there is.

792✭✭✭✭