metalguy21 said: s.g. is 1.15 and never rises.
I just did some quick numbers, 25 x 200w x .75 (overall efficiency) > ~ 3750W (actual) / 48v = ~ 78A max that your array will produce.....
The key is a load when there is NO charging occurring... between charge cycles..If I understand your earlier posts you have a constant draw all day... if it exceeds the total watts passing through the charge controller or Inverter chargers, then yes you are always draining the battery
No I produce around 4 times what I use while the sun shines. Thus my disappointment at the utilities ban on hybrid systems. Lots of sun left today so I'll give it a rest for the next couple hours and then EQ it once more.
OK, got the s.g. up to 1.255 after 4 hour genset absorb run and the rest of the day on solar. I'll check it again in the morning. I plan to kick the absorb voltage up to 59.0v and do another 4 hour absorb run w/genset very early. I have no heating problems at all and the gasing on absorb is major to say the least. At the rate things are going I believe I should see full charge by the end of the genset run and certainly by the end of the day. I also plan 2 or 3 more EQs now that I am at full charge.
I calc that at around 26kwh per day.