4 days ago I installed a GB Industrial 510 AH ( at 6 hours) 24 volt battery. I used a 15kw generator through the VFX3524 to boost it up to 100% charge so the trimetrec would show amount of charge Specific gravity was low so I thought I had a problem with my specific gravity tester, so it was 4 days till I could get a new one, and now I see it confirmed the first tester, The battery is at 1.150 an voltage at 24.9 The inverter shows fair as charge level, and the trimetric ( which was programmed for the new batt) shows 104% as state of charge. When I try to run the generator now the inverter shows an error light ( which it did not do before)
I am confused
Off grid, all solar, passive and active ( winter wood heat supplements) solar DHW, no backup.
Array 1 1980w, 12 Solarworld 165 w panels - Outback Flex max 80
Array 2 1590 w, 6 Solarworld 265 w panels - Outback flex max 60
Well array 600w, 6 Kyocera 130 w with Grundfos sqflex11 and cu200 to elevated storage, ( 2- 330 g tanks,) no battery storage at well
GB industrial 510 AH battery 24 V
Outback VFX 3525 inverter,