# Is DC Watts same as DC Watts?

lzhome
Posts:

**38**Registered Users ✭✭
Okay so I know for most this is a no brainer question so yes, I AM a new to most of this. I'm trying to size my electric load requirements before going forward with panels, batteries and so on.

So on my Kill A Watt meter when I see 40 Watts can I assume this converts to 40 Watts of DC power? At 24v?

So on my Kill A Watt meter when I see 40 Watts can I assume this converts to 40 Watts of DC power? At 24v?

TriStar MPPT, 8 x 100w PV, MNPV6 Combiner, 4 x 12v 155ah VMAXTanks AGMs and GoPower 2000w PSW Inverter.

0

#### Howdy, Stranger!

It looks like you're new here. If you want to get involved, click one of these buttons!

## Quick Links

#### Categories

- 23.5K All Categories
- 177 Forum & Website
- 87 Solar Forum News and Announcements
- 1.2K Solar News, Reviews, & Product Announcements
- 124 Solar Information links & sources, event announcements
- 786 Solar Product Reviews & Opinions
- 241 Solar Skeptics, Hype, & Scams Corner
- 18.4K Solar Electric Power, Wind Power & Balance of System
- 3.1K General Solar Power Topics
- 5.6K Solar Beginners Corner
- 813 PV Installers Forum - NEC, Wiring, Installation
- 1.7K Advanced Solar Electric Technical Forum
- 4.2K Off Grid Solar & Battery Systems
- 207 Caravan, Recreational Vehicle, and Marine Power Systems
- 867 Grid Tie and Grid Interactive Systems
- 542 Solar Water Pumping
- 721 Wind Power Generation
- 592 Energy Use & Conservation
- 202 Discussion Forums/Café
- 87 In the Weeds--Member's Choice
- 35 Construction
- 48 New Battery Technologies
- 32 Old Battery Tech Discussions
- 3.8K Solar News - Automatic Feed
- 3.8K Solar Energy News RSS Feed

## Comments

1,746Registered Users ✭✭✭✭2,310Registered Users ✭✭✭✭As Mcgivor notes, more watts need to be produced than are consumed by loads. How much more gets complicated.

Main daytime system ~4kw panels into 2xMNClassic150 370ah 48v bank 2xOutback 3548 inverter 120v + 240v autotransformer

Night system ~1kw panels into 1xMNClassic150 700ah 12v bank morningstar 300w inverter

949Solar Expert ✭✭✭✭4,529Solar Expert ✭✭✭✭38Registered Users ✭✭4,529Solar Expert ✭✭✭✭If you are running a fridge you should plan on 1Kwh +, I wouldn't run one on a 12 volt system.

27,432Super Moderators admin1,000 watt array * 0.52 system eff * 4.0 hours of sun = 2,080 watt*hours per day

-Bill

2,310Registered Users ✭✭✭✭Main daytime system ~4kw panels into 2xMNClassic150 370ah 48v bank 2xOutback 3548 inverter 120v + 240v autotransformer

Night system ~1kw panels into 1xMNClassic150 700ah 12v bank morningstar 300w inverter

27,432Super Moderators adminPower Factor is sort of like efficiency--But instead of being a pure loss, it is, sort of, how efficiently the AC current and AC voltage is being used.

An analogy--Peddling a bicycle. If you are peddling smoothly and apply force "in phase" with the peddles, that is the most efficient. Your PF=1.0

If, however, you sometimes peddle backwards for part of the cycle, or you "jump" on the peddles for part of the cycle, your PF~0.5 ... Your peddles+chain have to be 2x stronger to manage the irregular and extra force for part of the cycle. But you are not loosing any "efficiency" because, eventually, all of the force+RPM is being used to move the bicycle forward

Another analogy, pulling on a car with a rope. Standing in front of the car, 100% of your force is pulling the car forward. (Cosine 0 degrees = 1.0 = "PF"). Stand 60 degrees to the side, then only (COS 60 degrees=) 0.5 of the fource is moving the car forward, the rest is trying to pull the car sideways--But no work is being done, so no "loss of energy". The rope has to 2x stronger to pull the same car forward when standing to the side.

Similar with pulling for 1 second and not pulling for 1 second. 1/2 the cycle you are pulling forward, 1/2 the cycle you are not--The rope has to be twice a strong to do the same amount of work as standing in front of the car.

In the AC power world, some items have a natural near 1.0 PF... Heating elements and filament bulbs are example. Others have a vary poor PF--For example Cheap Twisty Florescent Bulbs may have a 0.5-0.6 PF. Electric induction motors may have a PF of ~0.6 to 0.8

Computer power supplies may have a PF~0.6-0.7, but "power factor corrected" power supplies generally have a PF~0.95 (close enough to perfect 1.0).

When you measure AC voltage and AC current--Then the proper equation is VA=V*I ... Your "simple meter" cannot measure the "phase between" voltage and current (that P=Watts=Volts*Amps*Cos phase angle between current and voltage). You need a special "Power Meter" to measure both at the same time to give you an accurate Watts calculation.

Why does it matter? Wiring, transformer, AC inverter outputs, Generators, and even utility lines, need to be design heavier to support the possible out of phase current (and non-sine wave current draw for computer/electronic power supplies). So, V*A is good for the wiring/system design. AC motor example:

- 10 amps AC * 1/0.60 "bad PF" = 16.7 Amps
- 120 VAC * 16.7 amps = 2,004 VA
- Watts = V*A*PF = 120 VA * 16.7 amps * 0.60 PF = 1,202 Watts

Now, for the DC input to your AC inverter--More or less, the Inverter only converts "power" (or Watts), bad VA on the output does not show up on the DC input as power usage--So the above DC calculation would be:- 1,202 Watts AC * 1/0.85 typical AC inverter efficiency = 1,414 Watts DC battery bus power
- 1,414 Watts DC power * 1/12 volt AC inverter input voltage = 118 Amps DC input current

There are more details, but that is the basics.The summary... Use V*A to calculate wiring AWG, transformers, AC inverter and Genset VA size (if no VA given, assume VA output = Watts name plate rating). To calculate the size of the battery bank, solar panels, and generator fuel usage, use Watt*Hours (power*hours of energy usage).

-Bill

949Solar Expert ✭✭✭✭