# Newbie project

System
Posts:

**2,511**admin
Eventually, we are going to move to an off-grid location, so I figured I'd try a little project to get started. Before I go further, I know I could do this less expensively by just trenching from the house's grid system - I just want to attempt this. Anyhow...

We have just purchased a wireless pet barrier for the dog. Basically, it shoots a radio frequency to the collar. When the collar is out of range, it starts to beep. If the dog continues past the beeps, he gets a correction shock. The system radiates from a central location from a few feet in diameter, to about 1/2 acre. My thought is to build a doghouse in about the center of the yard, giving him the maximum room to roam. I am thinking of designing the size of the dog house around the solar panel(s) if need be. I'd pitch the roof to the proper declination.

Here are my calculations, so feel free to correct anything you feel is wrong - thanks!

I measured the maximum draw on this unit, which is .17amps at 120VAC. Since the dog will not be outside 24 hours/day, I found a wireless remote control with a

6 amp/12V relay. My calculations so far figuring some inverter loss are based on .2amps @120Volts.

120V X .2a = 24 watts

24 watts X 12 hours(maximum) = 288 watts/day so I'll use 300watts

Location = 4.29 hours per day (avg) sunlight

Assuming the 300 watts/day and 4 hours of sun, I'm thinking a 100 watt panel would suffice. I already have a 12VDC to 120VAC converter (200 watt - sine wave) that I can use.

Here's where I start getting lost (I think).

Battery size: .2amps X 12V = 2.4AH. Now that I'm using a 12 volt system, I must multiply the 2.4AH by 10, which equals 24AH. I would assume that a 50% load would bring me to 48AH. If I wanted to store a couple days worth of charge, I'm looking at a 110AH battery.

A couple of other points:

1) The system would not run 12 hours/day 90% of the time

2) I always have the option of charging the battery to 90+% via a battery charger

Questions:

1) Would this panel be big enough to juice up the battery?

2) What type/size of charge controller would be recommended

Any other comments would be appreciated. Thanks in advance!

Would 1 - 100watt panel charge the battery effectively?

We have just purchased a wireless pet barrier for the dog. Basically, it shoots a radio frequency to the collar. When the collar is out of range, it starts to beep. If the dog continues past the beeps, he gets a correction shock. The system radiates from a central location from a few feet in diameter, to about 1/2 acre. My thought is to build a doghouse in about the center of the yard, giving him the maximum room to roam. I am thinking of designing the size of the dog house around the solar panel(s) if need be. I'd pitch the roof to the proper declination.

Here are my calculations, so feel free to correct anything you feel is wrong - thanks!

I measured the maximum draw on this unit, which is .17amps at 120VAC. Since the dog will not be outside 24 hours/day, I found a wireless remote control with a

6 amp/12V relay. My calculations so far figuring some inverter loss are based on .2amps @120Volts.

120V X .2a = 24 watts

24 watts X 12 hours(maximum) = 288 watts/day so I'll use 300watts

Location = 4.29 hours per day (avg) sunlight

Assuming the 300 watts/day and 4 hours of sun, I'm thinking a 100 watt panel would suffice. I already have a 12VDC to 120VAC converter (200 watt - sine wave) that I can use.

Here's where I start getting lost (I think).

Battery size: .2amps X 12V = 2.4AH. Now that I'm using a 12 volt system, I must multiply the 2.4AH by 10, which equals 24AH. I would assume that a 50% load would bring me to 48AH. If I wanted to store a couple days worth of charge, I'm looking at a 110AH battery.

A couple of other points:

1) The system would not run 12 hours/day 90% of the time

2) I always have the option of charging the battery to 90+% via a battery charger

Questions:

1) Would this panel be big enough to juice up the battery?

2) What type/size of charge controller would be recommended

Any other comments would be appreciated. Thanks in advance!

Would 1 - 100watt panel charge the battery effectively?

#### Howdy, Stranger!

It looks like you're new here. If you want to get involved, click one of these buttons!

## Quick Links

#### Categories

- 25.5K All Categories
- 198 Forum & Website
- 106 Solar Forum News and Announcements
- 1.2K Solar News, Reviews, & Product Announcements
- 146 Solar Information links & sources, event announcements
- 845 Solar Product Reviews & Opinions
- 246 Solar Skeptics, Hype, & Scams Corner
- 20.2K Solar Electric Power, Wind Power & Balance of System
- 3.3K General Solar Power Topics
- 6.1K Solar Beginners Corner
- 900 PV Installers Forum - NEC, Wiring, Installation
- 1.8K Advanced Solar Electric Technical Forum
- 4.7K Off Grid Solar & Battery Systems
- 333 Caravan, Recreational Vehicle, and Marine Power Systems
- 972 Grid Tie and Grid Interactive Systems
- 586 Solar Water Pumping
- 762 Wind Power Generation
- 609 Energy Use & Conservation
- 417 Discussion Forums/Café
- 192 In the Weeds--Member's Choice
- 62 Construction
- 81 New Battery Technologies
- 82 Old Battery Tech Discussions
- 3.8K Solar News - Automatic Feed
- 3.8K Solar Energy News RSS Feed

## Comments

30,178adminUsing the PV Watts program, assuming 1,000 watts of panels (sorry, smallest program will accept), 0.52 for system derating (yes, you really get 1/2 the rated panel power out the end of a 120 VAC inverter for an off-grid system). Assume Memphis, Tenn:

So, for a 100 watt panel, you are really looking at 1/10 of the above, or 5.4 to 8.7 kWhrs per month or:

- 5.4 kWhrs per month / 30 days = 0.18 kWH = 180 Watt*Hours per day winter
- 8.7 kWH per month / 30 days = 0.29 kWH = 290 WH per day summer peak

Also, you appeared to have measured 120 VAC Current into the wall transformer... Please note that P=V*I=Watts only for AC loads that look like a resistor.Many wall transformers look very inductive and tend to take current, but not power (Power Factor)... Basically the Cosine of the phase angle between voltage and current if you remember your physics or electrical classes from years past.

It is very possible that the wall transformer is using 1/2 the true power to operate. You can get a Kill-a-Watt meter to measure the true power (also good for measuring 120 VAC / 15 amps maximum loads throughout your home).

Your other option is to go with a DC conversion of the input power--it may use a lot less energy and you do not have the (very significant) inverter losses (inverters may have 6-8 watts of power just because they are on--will kill you at this low power levels). If you are going to be measuring a lot of smaller DC loads for your off-grid planning, one of these DC Amp*Hour/Watt*Hour meters may be very nice to have too.

Anyway, I have to go now--Questions?

-Bill

6,290adminThanks Bill!

Quick question.

The output of the power converter on the wireless fence system is 19VDC. If I measured the output side (19VDC), would I get the true power rating? If so, I'm not sure where I would get a 12VDC (or even a 24VDC) to 19VDC converter. Any ideas anyone?

30,178adminThe 19 VDC from a wall transformer is always a guess what the true voltage is when connected to the load (with filter capacitors, possibly rectifier).

And for volt meters, some measure the AC voltage and assume it is pure sine wave AC--and when you measure DC (like a battery), it will still read voltage on AC setting, etc... You almost need an oscilliscope on the the load's input and first stage power conditioning circuit to figure out what is going on (12 volts, 19 volts, 24 volts, etc.).

There are lots of various converters out there--You can get some of them from our host (NAWS 12/24 bidirectional converter). Without knowing the details of the load--it is very difficult to pick an appropriate device that is efficient (for the loads) and cost effective. You can also find a bunch of DC converters on www.digikey.com -- But you need to be somewhat electronically minded to pick one to try.

It is very possible that your "base station" will work just fine on 12 volts DC battery bank (really ~12-15 volts). But--I have no idea and would hate to see you smoke it experimenting.

You might try calling the mfg. and see if they have a battery option/suggestions on how to make a "portable" unit.

-Bill

8,653✭✭✭✭✭2 ideas about your 19V "wall wart"

1) look carefully at the back, molded in, should be text that says

12V 3W or DC 15V .2A

2) hook it up, and run power as normal. Get 2 sewing pins, about an inch apart, poke the pin into the low voltage wire from the wall wart to the wireless. Stick the other pin in the other wire, and measure voltage. Remove the pins, and the nearly invisible holes will be OK till the cord falls into a tank of water. But you know what the voltage is feeding the wireless shock collar.

|| Midnight Classic 200 | 10, Evergreen 200w in a 160VOC array ||

|| VEC1093 12V Charger | Maha C401 aa/aaa Charger | SureSine | Sunsaver MPPT 15A

solar: http://tinyurl.com/LMR-Solar

gen: http://tinyurl.com/LMR-Lister ,

6,290adminThanks for the info everyone!