# Easy to change system output to 124 volts from 120 volts with Outback FM80?

softdown
Solar Expert Posts:

**3,609**✭✭✭✭
I built a largish shop with two additional sub panels for the extra long runs. It is not unusual to only receive 117 volts with a standard load (such as refrigerator) on. I'd do better cranking out 124 volts than 120 volts.

I have six catalogs that often do more to confuse than to enlighten.Thought it was worth a quick question.

I have six catalogs that often do more to confuse than to enlighten.Thought it was worth a quick question.

First Bank:16 180 watt Grape Solar with FM80 controller and 3648 Inverter....Fullriver 8D AGM solar batteries. Second Bank/MacGyver Special: 10 165(?) watt BP Solar with Renogy MPPT 40A controller/ and Xantrex C-35 PWM controller/ and Morningstar PWM controller...Cotek 24V PSW inverter....forklift and diesel locomotive batteries

#### Categories

- 27.3K All Categories
- 226 Forum & Website
- 133 Solar Forum News and Announcements
- 1.3K Solar News, Reviews, & Product Announcements
- 174 Solar Information links & sources, event announcements
- 890 Solar Product Reviews & Opinions
- 251 Solar Skeptics, Hype, & Scams Corner
- 21.8K Solar Electric Power, Wind Power & Balance of System
- 3.5K General Solar Power Topics
- 6.6K Solar Beginners Corner
- 998 PV Installers Forum - NEC, Wiring, Installation
- 2K Advanced Solar Electric Technical Forum
- 5.3K Off Grid Solar & Battery Systems
- 420 Caravan, Recreational Vehicle, and Marine Power Systems
- 1K Grid Tie and Grid Interactive Systems
- 632 Solar Water Pumping
- 807 Wind Power Generation
- 619 Energy Use & Conservation
- 549 Discussion Forums/Café
- 255 In the Weeds--Member's Choice
- 86 Construction
- 103 New Battery Technologies
- 105 Old Battery Tech Discussions
- 3.8K Solar News - Automatic Feed
- 3.8K Solar Energy News RSS Feed

## Comments

469✭✭✭✭3,609✭✭✭✭3,609✭✭✭✭3,609✭✭✭✭953✭✭✭✭3,609✭✭✭✭The only time this issue comes into play is powering the well pump - where it only received 108 volts with the pump running. Now it should receive 113. Pretty long run to the well since it has to be 100' from the septic leach field.

But we had a poster claim that no harm was ever done when his equipment regularly ran on 90 volts. Opinions seem to vary. Don't they always?

953✭✭✭✭3,609✭✭✭✭There is speculation that well pump motors are designed to accommodate lower voltage since they always drop the voltage with their powerful motors. I still feel better at 113 than 108 volts.

It might prove to be a small amount of "free energy". Worth a try. Nothing to lose. I'm pretty certain my electronics are fine with 122-123 volts.

But I do not recommend going over 125 volt inverter output.

And - so far so good. I'm not going to scientifically verify a 2% gain in electrical efficiency. But I'll take it.

953✭✭✭✭3,609✭✭✭✭953✭✭✭✭3,609✭✭✭✭"If your loads are mostly resistive in nature, with a power factor close to 1.0 then it would make sense that raising the voltage increased the power used. Let's say you have 5 100 watt incandescent bulbs, rated at 120 volts. This works out to 500 watts / 120 volts = 4.1667 amps. 120 volts / 4.1667 amps = 28.8 ohms. Now we up the voltage to 125 volts. That same 28.2 ohm load now pulls 125 volts / 28.8 ohms = 4.3403 amps. 125 volts x 4.3403 amps = 542.53 watts. The power goes up at a square of the voltage in a resistive circuit. 120 to 125 volts is only a 4.1667% increase, but the wattage going from 500 to 542.53 is an 8.5% increase in power. If your inverter is 90% efficient, it was pulling 555 watts before, and now it needs 603 watts. This will certainly show up on the battery useage. On a 48 volt battery, this is 11.5 amps to 12.6 amps, just by raising the voltage 5 volts.

Not all loads are purely resistive. Some motors and such could be even worse and make more heat and use more power, or might get more efficient with a little more volts, it is hard to say for sure. Reactive and capacitive loads are not easilly predictable with changing supply voltage. But most will probably still take a little more power at a higher voltage. Modern switching regulated power supplies will still pull about the same power by pulling less current at the higher voltage, but an old style linear regulator will have to drop the voltage more and turn more power into heat to keep the same output voltage. Take an old 5 volt logic supply. They normally have about 7 volts before the regulator. If it is running at 10 amps, that is 50 watts to the load and 20 watts going out as heat from the regulator. 7 - 5 = 2 volts, x 10 amps = 20 watts. Raising the voltage going in by just the 4.1667% makes this look a lot worse. We now have 7.3 volts before the linear regulator. It still drops the output to 5 volts for 50 watts at the load, but now it is dropping 23 watts of heat instead of 20 watts. 7.3 - 5 = 2.3 volts x 10 amps = 23 watts. This is 15% more wasted power than before."

Think I'll try 118 volts next - never satisfied.