Conductors in “wet” location LFMC
Relating to LFMC’s 350.12(2).
Standard LFMC commonly has a UL listing of 60 degree c “wet” temperature rating.
Is the expectation that conductors passing through a 2’ section of LFMC in an outdoor location must now reference the 60 degree ampacity column?
Before being made aware I would have always sized based on OCPD’s 75 temp rating.