Bulk / Absorb question
My system has been running for about two weeks now and it seems (to me) to be running well. So far I'm only dipping into the batteries about 10% on average overnight (being overly conservative at first).
My bank is two 24v parallel strings of Rolls s550's and I've got them connected to a Midnite Classic 150.
Rolls states that the Bulk phase typically charges a bank to 80%. This has me slightly concerned since the default program of the classic has Bulk beginning in the early AM sun on a bank that is already at 90% SOC. Rolls also recommends the formula T = 0.42 x C /I for absorb time calculation - with the ~100a output of the classic, that puts my Absorb cycle at roughly 4 hours. This combination seems like it could be too much to replenish 10% usage.
Hoping for some opinions on whether or not some fine tuning would be a good idea or if all is a-o-k.