# Please help me double check my array modification.

Hairfarm
Solar Expert Posts:

**225**✭✭✭
Greetings,

I'm looking for some input about increasing my array size to better match my battery bank's amp hours. I'm a bit rusty and would appreciate it if someone could check my math before I make any purchases.

My current array looks like this:

Three strings @ 35.4 volts @ 22.8 amps for 810 watts. (Series raises voltage, parallel raises amps).

The current I can expect from 810 watts on an MPPT controller:

810 * 0.77 (typical efficiency) = 623 / 12-volt minimum battery Voltage = 52 amps.

My battery bank uses six 6V FLA batteries wired in series and then paralleled to make 696Ah. My 696Ah battery bank actually needs 69.6 amps to charge at a C/10 rate, (696 * .10 = 69.6). The 52 amps that my array makes now isn't enough for my 696Ah bank. This has been bugging me in the back of my mind for the last year. This is why I want to increase my array by adding two more panels: 135w Kyocera 17.7V @ 7.6A.

This will make my array like this now:

I would be reducing my array from three strings to two strings. Obviously I'll have an extra string's worth of wire just sitting idle in my conduit after the modification, but no big deal right? This was the best configuration I could come up with that can make 8 panels work.

So now it will be: 1080w * .77 = 831.6w / 12 = 69.3Ah. And my 696Ah battery bank needs 69.6 amps. Almost perfect for a C/10 rate, right? Any problems with my math or other issues?

Btw, I'm using an MPPT 80A Outback controller. Even with my array pushing almost 70A I still have a 10A buffer before my CC reaches its 80A maximum capacity.

thanks!

hairfarm

I'm looking for some input about increasing my array size to better match my battery bank's amp hours. I'm a bit rusty and would appreciate it if someone could check my math before I make any purchases.

My current array looks like this:

Three strings @ 35.4 volts @ 22.8 amps for 810 watts. (Series raises voltage, parallel raises amps).

The current I can expect from 810 watts on an MPPT controller:

810 * 0.77 (typical efficiency) = 623 / 12-volt minimum battery Voltage = 52 amps.

My battery bank uses six 6V FLA batteries wired in series and then paralleled to make 696Ah. My 696Ah battery bank actually needs 69.6 amps to charge at a C/10 rate, (696 * .10 = 69.6). The 52 amps that my array makes now isn't enough for my 696Ah bank. This has been bugging me in the back of my mind for the last year. This is why I want to increase my array by adding two more panels: 135w Kyocera 17.7V @ 7.6A.

This will make my array like this now:

I would be reducing my array from three strings to two strings. Obviously I'll have an extra string's worth of wire just sitting idle in my conduit after the modification, but no big deal right? This was the best configuration I could come up with that can make 8 panels work.

So now it will be: 1080w * .77 = 831.6w / 12 = 69.3Ah. And my 696Ah battery bank needs 69.6 amps. Almost perfect for a C/10 rate, right? Any problems with my math or other issues?

Btw, I'm using an MPPT 80A Outback controller. Even with my array pushing almost 70A I still have a 10A buffer before my CC reaches its 80A maximum capacity.

thanks!

hairfarm

#### Categories

- 25.8K All Categories
- 200 Forum & Website
- 108 Solar Forum News and Announcements
- 1.2K Solar News, Reviews, & Product Announcements
- 148 Solar Information links & sources, event announcements
- 853 Solar Product Reviews & Opinions
- 246 Solar Skeptics, Hype, & Scams Corner
- 20.4K Solar Electric Power, Wind Power & Balance of System
- 3.3K General Solar Power Topics
- 6.2K Solar Beginners Corner
- 915 PV Installers Forum - NEC, Wiring, Installation
- 1.9K Advanced Solar Electric Technical Forum
- 4.8K Off Grid Solar & Battery Systems
- 348 Caravan, Recreational Vehicle, and Marine Power Systems
- 978 Grid Tie and Grid Interactive Systems
- 595 Solar Water Pumping
- 774 Wind Power Generation
- 610 Energy Use & Conservation
- 449 Discussion Forums/Café
- 212 In the Weeds--Member's Choice
- 70 Construction
- 83 New Battery Technologies
- 84 Old Battery Tech Discussions
- 3.8K Solar News - Automatic Feed
- 3.8K Solar Energy News RSS Feed

## Comments

3,738✭✭✭✭--vtMaps

225✭✭✭Besides I don't have any more room in my conduit for a set of wires for a fourth string

8,817✭✭✭✭✭Put the PV combiner at the array, 4 breakers, 2s panels, 4p strings and keep the voltage the same, Run a single pair wires from combiner to the controller in the conduit, wire lasts forever, charge controllers burn out.

That would be 30A 8ga or 6ga wire depending on the length

See if you can locate the array voltage/battery voltage/efficiency chart.

I'm not happy running 160V into my 200V classic for 48V battery. Runs hot and fans scream all the time.

|| Midnight Classic 200 | 10, Evergreen 200w in a 160VOC array ||

|| VEC1093 12V Charger | Maha C401 aa/aaa Charger | SureSine | Sunsaver MPPT 15A

solar: http://tinyurl.com/LMR-Solar

gen: http://tinyurl.com/LMR-Lister ,

3,738✭✭✭✭To answer your question, let's take the input power to be 750 watts. With two panels in series the controller will be 94.5% efficient and 41.25 watts (of the 750) will heat up the controller. With four panels in series the controller will be 93.5% efficient and 48.75 watts (of the 750) will heat up the controller.

Your proposed array size is at or over the limit for that controller in a 12 volt system. And as mentioned, as you approach the limits the controller becomes less efficient.

Glad to oblige (from the manual):

--vtMaps

225✭✭✭At 1080 watts of array it looks like my efficiency is around 93% according to that graph.

Btw, according to the manual the Flexmax 80 can handle an array size up to 1250w for a 12 volt system, page 76.

I'd like to go to a 24 volt system but then my battery bank would need to go from 6 batts currently to 8, (or down to four).

thanks!