# voltage drop calculator confusion

muddome
Registered Users Posts:

**9**✭
I'm confused on what value to enter for my voltage on the NAWS voltage drop calculator.

http://www.windsun.com/Hardware/Voltage_Calc.htm

Do I use my system voltage which is 24v or do I use the Voc from my panels prallel strings which is 133?

Also is the distance one way?

http://www.windsun.com/Hardware/Voltage_Calc.htm

Do I use my system voltage which is 24v or do I use the Voc from my panels prallel strings which is 133?

Also is the distance one way?

#### Howdy, Stranger!

It looks like you're new here. If you want to get involved, click one of these buttons!

## Quick Links

#### Categories

- 25.2K All Categories
- 194 Forum & Website
- 102 Solar Forum News and Announcements
- 1.2K Solar News, Reviews, & Product Announcements
- 145 Solar Information links & sources, event announcements
- 838 Solar Product Reviews & Opinions
- 246 Solar Skeptics, Hype, & Scams Corner
- 19.9K Solar Electric Power, Wind Power & Balance of System
- 3.3K General Solar Power Topics
- 6.1K Solar Beginners Corner
- 887 PV Installers Forum - NEC, Wiring, Installation
- 1.8K Advanced Solar Electric Technical Forum
- 4.6K Off Grid Solar & Battery Systems
- 323 Caravan, Recreational Vehicle, and Marine Power Systems
- 957 Grid Tie and Grid Interactive Systems
- 581 Solar Water Pumping
- 751 Wind Power Generation
- 608 Energy Use & Conservation
- 363 Discussion Forums/Café
- 161 In the Weeds--Member's Choice
- 58 Construction
- 74 New Battery Technologies
- 70 Old Battery Tech Discussions
- 3.8K Solar News - Automatic Feed
- 3.8K Solar Energy News RSS Feed

## Comments

29,717adminThe distance appears to be one way (using another calculator with same numbers).

You use the "nominal" or "minimum" operational voltage/maximum current expected at each point in your system.

If is your battery bank--The worst case is ~21 volts for a low battery/high current/high voltage drop (assuming AC input to your inverter).

For the solar array, it can be the Vmp-array-hot, or it can be a volt or two above Vbatt-charging--An MPPT controller would be Vmp-array. For a PWM (less expensive controller), the voltage would be ~Vbatt-charging.

It just depends on how conservative you want to get--Hot copper wire has higher resistance, etc... You will get close enough if you use "nominal" numbers too.

Voltage drop, for example, on a 12 volt battery bank. Assume battery minimum voltage ~11.5 volts and 10.5 volts minimum for inverter operation. The difference is ~1.0 volt drop.

For a 1,200 watt AC inverter, the maximum worst case current would be:

1,200 watts * 1/10.5 volts cutoff * 1/0.85 inverter efficiency = 134.5 amp maximum worst case current @ 1,200 watts

And, most "good quality" AC inverters will power ~2x rated load for a few seconds (starting a pump for example)--So, you the worst case current could be as high as 269 amps... Therefore, you could use 0.5 volts as your maximum "nominal" voltage drop for a 12 volt battery bank (to allow 2x surge current). Or:

0.5 volt/12 volts = ~0.04 = 4% maximum drop

-Bill

PS: To make it clear, Voc (voltage open circuit) would not be your base voltage--Since there is no current flow. You actual voltage drop would be Vmp-array (close enough).