Ground conductor patterns
The NEC states that a continuous ground conductor has to be used to ground the panels in a string. I understand the intent is so that when disconnecting a single panel, you don't interrupt the ground to the rest of the string. I've drawn two diagrams below that may meet that requirement. Can I get some feedback as to how the following two grounding patterns are interpereted by the NEC? Can either be used?
0 · Share on Twitter