# voltage drop 12- 15 ft inverter cables

Solar Expert Posts: 50 ✭✭✭✭
What would the voltage drop be from 12- 15 ft 4/0 cable from inverter to battery bank?

what would be the proper method of dealing with this issue?

is 4/0 good enough to negate that?

• Solar Expert Posts: 9,359 ✭✭✭✭✭
Re: voltage drop 12- 15 ft inverter cables
John XW NY wrote: »
What would the voltage drop be from 12- 15 ft 4/0 cable from inverter to battery bank?

what would be the proper method of dealing with this issue?

is 4/0 good enough to negate that?

Depends on the Amps drawn, more amps = more drop
Powerfab top of pole PV mount | Listeroid 6/1 w/st5 gen head | XW6048 inverter/chgr | Iota 48V/15A charger | Morningstar 60A MPPT | 48V, 800A NiFe Battery (in series)| 15, Evergreen 205w "12V" PV array on pole | Midnight ePanel | Grundfos 10 SO5-9 with 3 wire Franklin Electric motor (1/2hp 240V 1ph ) on a timer for 3 hr noontime run - Runs off PV ||
|| Midnight Classic 200 | 10, Evergreen 200w in a 160VOC array ||
|| VEC1093 12V Charger | Maha C401 aa/aaa Charger | SureSine | Sunsaver MPPT 15A

solar: http://tinyurl.com/LMR-Solar
gen: http://tinyurl.com/LMR-Lister ,

Re: voltage drop 12- 15 ft inverter cables

Assuming a XW 4024 used at full capacity (8kW surge?), 85% inverter efficiency, and 21 volt minimum:

Amps = 8,000 watts * 1/21 volts min * 1/0.85 eff = 448 amps maximum

You have 15' run of cable, and for this calculator (voltage drop calculator) , use 2x15'=40' of wire, 100F--you get:

Drop= 0.70 volts
%Drop= 2.94% (based on 24 volts)

For 4kW max operating current, 0.35 volts and 1.47% drop.

In general, keeping those heavy current leads between charge controllers and inverter to the batteries as short as practicable is a good idea.

-Bill
Near San Francisco California: 3.5kWatt Grid Tied Solar power system+small backup genset