250 VDC termination
I have an Anderson connection at the end of a relatively long length of 2 two10 g wires (in split wire loom) that I want to terminate at a safe location and shorten it. I do not need the service, but getting to the source terminals is quite difficult. Is there a safe way to shorten and terminate permanently? It is a protected environment from access, vibration, excessive heat, water, etc.,etc. The service is at 250 VDC.
3850 watts - 14 - 275SW SolarWorld Panels, 4000 TL-US SMA Sunny Boy Grid tied inverter. 2760 Watts - 8 - 345XL Solar World Panels, 3000 TL-US SMA Sunny Boy GT inverter. 3000 watts SMA/SPS power. PV "switchable" to MidNite Classic 250ks based charging of Golf cart + spare battery array of 8 - 155 AH 12V Trojans with an APC SMT3000 - 48 volt DC=>120 Volt AC inverter for emergency off-grid. Also, "PriUPS" backup generator with APC SURT6000/SURT003 => 192 volt DC/240 volt split phase AC inverter.
0 · Share on Twitter