Inverter losses
mountainman
Registered Users Posts: 439 ✭✭
When sizing a battery bank to loads. Does the 85℅ account for inverter idle. My loads are 1100 wh daily. .85 inverter efficiency puts me at 1294 whs . My 300 pure sine uses 8 watts just being on x24 hrs.~200 whs. Do I add this also 1294 +200=1494? Or is it already included in the 85℅??
2kw array 6 345 q cells make sky blue 60 cc
6 230ah GC @36 volts
18 amp accusense charger. 3650 champion
6 230ah GC @36 volts
18 amp accusense charger. 3650 champion
Comments

The 0.85 does include inverter losses... But that is pretty much assuming that the inverter is reasonably loaded when turned on. If, for example, you have a load you run for 5 hours per night, but leave the inverter running 24x7, then you should add in the tare losses too...
For example, say you run a 100 Watt AC load on your 3009 Watt inverter for 5 hours per night and run the inverter 24 hours per day... Very roughly: 100 Watts * 0.85 inverter eff * 5 hours per night = 588 Watt*hours at the battery bus
 8 Watts * 20 hours per night = 160 WH per day
 588 Watts + 160 Watts = 740 WH per day
 100 Watts * 5 hours = 500 WH load
 500 WH load / 740 WH est. battery bus load = 0.68 = ~68% efficiency
https://2n1s7w3qw84d2ysnx3ia2bctwpengine.netdnassl.com/wpcontent/uploads/2014/02/SureSineENG_R2_1_08.pdf
I use 85% efficiency to allow for less than optimum inverter usage. However, if you operate "outside" an assumed standard loading... Then the 85% is not accurate.
One of the nice things about this MorningStar inverter, is that it has search mode (AC load less than ~8 Watts, the inverter goes into Search mode that consumes ~55 milliamps: 0.055 Amps * 12 volts = 0.66 Watts
 0.66 Watts * 20 Hours per day = 13.2 WH per day (20 hours in standby)
 500 WH load / (588 WH loaded + 13.2 WH standby) = 0.83 ~ 83% Efficiency
Bill
Near San Francisco California: 3.5kWatt Grid Tied Solar power system+small backup genset 
This a 24 hr load. unless we are away.
Then I Turn it off. A 20 inch box fan a led tv. and 2 phone chargers. The fan runs 12 hrs a night. and the tv all day.
~50 watt constant load.
I did a couple weeks test to get an average daily use.
As an experiment couldn't I hook a dc watt meter from the battery to the inverter.
And compare dc wh to ac wh for more accurate results. and see the true conversion efficiency for my system?2kw array 6 345 q cells make sky blue 60 cc
6 230ah GC @36 volts
18 amp accusense charger. 3650 champion 
Thanks for the link when my 3 year old.... dreaded word on this forum. aims converter that specs 95℅ 1/3 load 90℅ full load .7 amp idle goes out. I'll get me one.2kw array 6 345 q cells make sky blue 60 cc
6 230ah GC @36 volts
18 amp accusense charger. 3650 champion 
If it works for you, that's great!
Offgrid.
Main daytime system ~4kw panels into 2xMNClassic150 370ah 48v bank 2xOutback 3548 inverter 120v + 240v autotransformer
Night system ~1kw panels into 1xMNClassic150 700ah 12v bank morningstar 300w inverter 
Yes, with an AC and DC side Watt*hour meters, you will get more accurate numbers...
However, the power numbers will probably be something like 5% 10% level of accuracy between all of the different measurement devices. And add the issues of waveforms and phase angle measurementsDoes not help with accuracy.
Looking at the math and your pattern of energy usageAt least you can figure out what is important to you, and how much you may have to compensate for things like 24x7 AC power (vs size of battery bank, solar array, etc.).
BillNear San Francisco California: 3.5kWatt Grid Tied Solar power system+small backup genset 
Our inverter is the Schneider SW4024. I may have been overly conservative, but in my design I used 85% efficiency for the inverter (which contributed to an overall efficiency of the system of 50%), but I also included 26W continuous tare loss in the energy budget. 26W x 24 hrs/day added 624 watt hours to the overall daily consumption.
Offgrid cabin: 6 x Canadian Solar CSK280M PV panels, Schneider XWMPPT60150 Charge Controller, Schneider CSW4024 Inverter/Charger, Schneider SCP, 8S (25.6V), 230Ah Eve LiFePO4 battery in a custom insulated and heated case. 
Horsefly said:Our inverter is the Schneider SW4024. I may have been overly conservative, but in my design I used 85% efficiency for the inverter (which contributed to an overall efficiency of the system of 50%), but I also included 26W continuous tare loss in the energy budget. 26W x 24 hrs/day added 624 watt hours to the overall daily consumption.1500W, 6× Schutten 250W Poly panels , Schneider MPPT 60 150 CC, Schneider SW 2524 inverter, 400Ah LFP 24V nominal battery with Battery Bodyguard BMS
Second system 1890W 3 × 300W No name brand poly, 3×330 Sunsolar Poly panels, Morningstar TS 60 PWM controller, no name 2000W inverter 400Ah LFP 24V nominal battery with Daly BMS, used for water pumping and day time air conditioning.
5Kw Yanmar clone single cylinder air cooled diesel generator for rare emergency charging and welding. 
mcgivor said:Horsefly said:Our inverter is the Schneider SW4024. I may have been overly conservative, but in my design I used 85% efficiency for the inverter (which contributed to an overall efficiency of the system of 50%), but I also included 26W continuous tare loss in the energy budget. 26W x 24 hrs/day added 624 watt hours to the overall daily consumption.Offgrid cabin: 6 x Canadian Solar CSK280M PV panels, Schneider XWMPPT60150 Charge Controller, Schneider CSW4024 Inverter/Charger, Schneider SCP, 8S (25.6V), 230Ah Eve LiFePO4 battery in a custom insulated and heated case.

Things like higher battery bus voltage causes more current draw because of the capacitance of the FETs. Also, possibly because of 50 vs 60 Hz switching (higher frequency (again, more switching across capacitance of FETs, etc.).
BillNear San Francisco California: 3.5kWatt Grid Tied Solar power system+small backup genset 
Been looking at the suresine efficiency charts.
Seems at a 50100 watt load efficiency is slightly higher. Then at 50℅ it declined. While looking at other inverters after 50℅ load they also declined
So for smallish loads seems it would be more efficient to size your inverter 23x the size of your max load?2kw array 6 345 q cells make sky blue 60 cc
6 230ah GC @36 volts
18 amp accusense charger. 3650 champion 
For larger systems (mutli kWatt off grid systems), the lesser efficiency of smaller loads is a "don't care".
However, this always assumes a "balanced" system design. (more or less, C/8 to C/20 discharge rates for battery bank, C/8 to C/10 solar charging, etc.).
When you have something "different" such high surge loads for short periods of time on a small battery bank (AGM or Li Ion for high surge) and relatively small solar array, then the large AC inverter with (on average) small AC loads, then the Tare losses of the inverter do matter a lot and running the inverter 24x7 becomes a very significant load (sometimes on the order of 1/3 to 1/2 of the entire "solar" load).
For small systems, you have to look closely at all loads (including "vampire loads" that are on all the time, but not in use all the timeSuch as wall warts, AC inverters with no loads at times, etc.).
On a 500 WH per day system, a 6 Watt AC inverter (like the MorningStar) on 24x7: 6 Watts * 24 hours per day = 144 Watt*Hours per day
 144 WH / 500 WH = 29% of "system design" is used just to run a 6 Watt Tare load on an inverter 24x7
 0.025 Amps * 12 volts = 0.3 Watts ("remote off")
 0.055 Amps * 12 volts = 0.66 Watts ("search mode standby")
 0.66 Watts * 24 hours per day = 15.84 WH per day (search mode)
 15.84 WH per day / 500 WH per day system design = 3% of system capacity using "search mode"
https://www.solarelectric.com/morningstarsi300115vulinverter.html
Now, some of the Cotek (and similar?) smaller inverters come with search/remote controls (and some even have remote panels):
https://www.solarelectric.com/cotekse200112puresinewaveinverter.html
The right tool for the right job...
BillNear San Francisco California: 3.5kWatt Grid Tied Solar power system+small backup genset 
The stand by function interest me.
my radio only pulls 10 watts I wonder how accurate that 8 watt search is.
Would it sense 10 watts?
Everything that runs on ac is 150 watts on the kil o watt meter.
So Im thinking the 300 would be a better match than the 200 cotek?
With a 5600 watt p/day design such as mine. Every little bit counts
With just the inverter adding up to ~35℅ of my useage. Seems Im forever turning the inverter off and on trying to conserve.
Would be convenient to just leave it on.2kw array 6 345 q cells make sky blue 60 cc
6 230ah GC @36 volts
18 amp accusense charger. 3650 champion 
The MorningStar does not have any fans... I like that.
Would I bet the farm on 10 Watts vs 8 Watts "searchmode on"? Probably not... However, you could run the remote on off around and place switches near the major loads (radio, etc.) and simply turn on when needed.
You could probably do something "interesting" like a motion detector that "turns on" the inverter when you are around.
Or a simple timer that turns on the inverter when you are around the house (say 5pm to 10pm) and let the search mode manage for other times (larger loads, etc.).
And there is the old twist timerTwist on for a period of time (say one or two hours) to charge the cell phone/tablet computer/lower power LED light and then shuts off automatically so you don't have to remember (presumably search mode will keep any loads >~8 watts on until they are shut off).
BillNear San Francisco California: 3.5kWatt Grid Tied Solar power system+small backup genset 
My MS 300w inverter seems to sense the 8w or whatever pretty well. Turning on an LED bulb (~10w IIRC) in the bathroom wakes it up.Offgrid.
Main daytime system ~4kw panels into 2xMNClassic150 370ah 48v bank 2xOutback 3548 inverter 120v + 240v autotransformer
Night system ~1kw panels into 1xMNClassic150 700ah 12v bank morningstar 300w inverter 
Thanks that's good to know. I see it accepts 2awg . As far as voltage drop should I shoot for something like .05 with 6 foot of 2 awg? Or .12 with 6awg?2kw array 6 345 q cells make sky blue 60 cc
6 230ah GC @36 volts
18 amp accusense charger. 3650 champion 
Generally, a maximum of 0.5 volt drop for 12 volt wiringI would suggest. Less drop certainly is less losses. Probably a 1% loss (~0.12 volt drop) is the maximum that it is "worth" cabling for:
 0.5 volts * 50 Amps DC (~600 Watts) = 25 Watt cable loss.
https://www.calculator.net/voltagedropcalculator.html
BillNear San Francisco California: 3.5kWatt Grid Tied Solar power system+small backup genset
Categories
 All Categories
 222 Forum & Website
 130 Solar Forum News and Announcements
 1.3K Solar News, Reviews, & Product Announcements
 189 Solar Information links & sources, event announcements
 886 Solar Product Reviews & Opinions
 254 Solar Skeptics, Hype, & Scams Corner
 22.3K Solar Electric Power, Wind Power & Balance of System
 3.5K General Solar Power Topics
 6.7K Solar Beginners Corner
 1K PV Installers Forum  NEC, Wiring, Installation
 2K Advanced Solar Electric Technical Forum
 5.5K Off Grid Solar & Battery Systems
 424 Caravan, Recreational Vehicle, and Marine Power Systems
 1.1K Grid Tie and Grid Interactive Systems
 651 Solar Water Pumping
 815 Wind Power Generation
 621 Energy Use & Conservation
 608 Discussion Forums/Café
 302 In the WeedsMember's Choice
 74 Construction
 124 New Battery Technologies
 108 Old Battery Tech Discussions
 3.8K Solar News  Automatic Feed
 3.8K Solar Energy News RSS Feed