# Solar charging series or parallel for MPPT to 12v battery

gqroot
Registered Users Posts:

**22**✭
Hi folks,

I am building a off-grid system to power up 12 watt device running 24 hrs. The build of materials below. I am wondering if I should get a pair of 12v 100 watt panel in series or in parallel to charge my 12v battery. I get about 2 hours of sun and trying to spec it for 2 days without the sun. Is it better to have the solar panel in series or in parallel when the cable run is 25 feet?

1x MorningStar SunSaver SS-MPPT-15L Charge Controller

1x Concorde PVX-340T Sun Xtender Solar Battery 12V

2x 12v 100w Solar Panel

Thanks in advance!

I am building a off-grid system to power up 12 watt device running 24 hrs. The build of materials below. I am wondering if I should get a pair of 12v 100 watt panel in series or in parallel to charge my 12v battery. I get about 2 hours of sun and trying to spec it for 2 days without the sun. Is it better to have the solar panel in series or in parallel when the cable run is 25 feet?

1x MorningStar SunSaver SS-MPPT-15L Charge Controller

1x Concorde PVX-340T Sun Xtender Solar Battery 12V

2x 12v 100w Solar Panel

Thanks in advance!

#### Categories

- 26.8K All Categories
- 215 Forum & Website
- 123 Solar Forum News and Announcements
- 1.3K Solar News, Reviews, & Product Announcements
- 166 Solar Information links & sources, event announcements
- 878 Solar Product Reviews & Opinions
- 251 Solar Skeptics, Hype, & Scams Corner
- 21.4K Solar Electric Power, Wind Power & Balance of System
- 3.4K General Solar Power Topics
- 6.5K Solar Beginners Corner
- 975 PV Installers Forum - NEC, Wiring, Installation
- 1.9K Advanced Solar Electric Technical Forum
- 5.2K Off Grid Solar & Battery Systems
- 394 Caravan, Recreational Vehicle, and Marine Power Systems
- 1K Grid Tie and Grid Interactive Systems
- 625 Solar Water Pumping
- 796 Wind Power Generation
- 616 Energy Use & Conservation
- 513 Discussion Forums/Café
- 238 In the Weeds--Member's Choice
- 84 Construction
- 99 New Battery Technologies
- 92 Old Battery Tech Discussions
- 3.8K Solar News - Automatic Feed
- 3.8K Solar Energy News RSS Feed

## Comments

32,005admin[note: I messed up here--25 feet and 12 watts--See following post for corrections]That battery seems awfully small for your application (12 volt @ 34 Amp*Hours??):

- 12 volts * 34 AH * 1/25 watt load = 16.3 hours until "dead"

If you want to go 2 days without sun and 50% maximum discharge (for longer battery cycle life):- 25 watts * 24 hours per day * 1/12 volt battery bank * 2 days * 1/0.50 maximum discharge = 200 Amp*Hour @ 12 volt battery bank

You may want to look at using 2x 6 volt @ ~200 AH golf cart batteries--At least for the first try. They may be a lot cheaper and easier to monitor (can use a hydrometer, add distilled water once a month). Once you get the system stable and working the way you want--Eventually replace with AGM (more expensive, less maintenance, perhaps a bit shorter cycle life).-Bill

22✭32,005adminOf course, that gets security questions (if a problem). Possibly place the electrical box at a lower height (use a ladder).

And "Oops...". I got my numbers mixed up, you are running 12 Watts, not 25 watts--Mixed the numbers up in my earlier post:

- 12 volts * 34 AH * 1/12 watt load = 34 hours until "dead"
- 12 watts * 24 hours per day * 1/12 volt battery bank * 2 days * 1/0.50 maximum discharge = 96 Amp*Hour @ 12 volt battery bank

Sorry.- 12 watts * 24 hours per day * 1/0.77 charge controller+panel derating * 1/0.90 AGM batt eff * 1/2 hours of sun per day = 208 Watt array minimum
- 96 AH battery bank * 14.5 volts charging * 1/0.77 panel+controller derating * 0.10 rate of charge = 181 Watt array recommended minimum size (10% rate of charge)

So, a pair of ~100 Watt panels would appear to fit the minimum requirements.You started this as a wiring length question--Solar panels mounted on pole? And yes, I probably would use the two solar panels in series to allow a smaller awg wire. Using a generic voltage drop calculator:

- 2 * 100 Watt panels * 1/35 volts Vmp-array = ~5.71 amps Imp

http://www.calculator.net/voltage-drop-calculator.html for 3% to ~1% maximum drop- 0.03 maximum recommended voltage drop * 35 volts Vmp-array = 1.05 volt maximum drop

Using voltage drop calculator with 25 feet one way run and 5.71 amps and 1.05 maximum voltage drop:14 AWG wire:

Voltage drop:

0.72Voltage drop percentage:

2.06%Voltage at the end:

34.2810 AWG wire:

Voltage drop:

0.29Voltage drop percentage:

0.83%Voltage at the end:

34.71So, I would suggest around 14-10 AWG wire as being optimum for this installation.

-Bill

22✭