TnAndy wrote: »
Hmmm.....reckon they cut the panel lead end connectors off and crimped a connector on the extensions ?
Be intesting to see your sketch and some photos.
Starting to sound like a horror story in the making....ahahaaaaaa
Note: In every illustration in the install manual pictures a power distribution box along with the inverter. There isn't one ! Just an inverter and some wiring.
6 pv's in series would create 135 v which is under the rating of 150 for the controller.
Solar Guppy wrote: »
GEL is a Superior battery to flooded in every measurable way, they cost 2x for a reason. .....
Cariboocoot wrote: »
Just to help out, the actual specs on the Evergreen ES-A 200 panels:
Voc 22.6, Vmp 18.1, Imp 11.05, Isc 11.8
A string of six would be:
Voc 135.6 (safely below the controller's 150 Max unless it gets very cold) and Vmp 108.6