Does this section apply to EGC's for solar panel frame grounding in ground mount and carport structure applications? I think it is a question of code interpretation whether the ground conductor is physically protected from physical damage. There are even those Tyco Solklips that can only accept a #10-12 ground anyway so having to use a #6 would not even make sense. Any thoughts, inputs, suggestions?
0 · Share on Twitter