# Wire sizing

sridharTS
Registered Users Posts:

**33**✭
How to choose the wire guage for solar sytem in accordance with volts,amps and feet

sridharTS
Registered Users Posts: **33** ✭

How to choose the wire guage for solar sytem in accordance with volts,amps and feet

## Comments

3,741✭✭✭✭--vtMaps

767✭✭✭✭What the voltage and amps you think it will run?

Remember a 1 volt drop across wires in a 12 volt system is double the power loss of a 24 volt system and 4 times the loss in a 48 volt setup.

A 1 volt drop is about the absolute max you want to see in a 12 volt system. If you have a 1 volt drop on your 12 volt system you just wasted 6% to 8% of your power on heating up the wires.

Solar hybrid gasoline generator, 7kw gas, 180 watts of solar, Morningstar 15 amp MPPT, group 31 AGM, 900 watt kisae inverter.

Solar roof top GMC suburban, a normal 3/4 ton suburban with 180 watts of panels on the roof and 10 amp genasun MPPT, 2000w samlex pure sine wave inverter, 12v gast and ARB air compressors.

33✭32,601adminSay you have a 1,200 Watt solar array with Vmp~17.5 volts per panel. You can put them in parallel to charge a 12 volt battery bank with a PWM solar charge controller, or you can put them in series/parallel with a MPPT charge controller (higher end controllers are around 100 Volts max for Vmp):

- 1,200 Watts / 17.5 volt Vmp per panel = 69 Amps Imp-array

Using a generic voltage drop calculator like this:http://www.calculator.net/voltage-drop-calculator.html

If we want a maximum of 1-3% voltage drop (typical for solar) and want to run the wiring ~33 feet (~10 meters) from panels to charge controller):

- 17.5 volts * 0.03 volt drop = 0.525 volt drop maximum, 69 amps, and 33 feet--Voltage drop calculator would tell us:

1/0 copper cable (would give numbers below)Voltage drop:

0.45Voltage drop percentage:

2.57%Voltage at the end:

17.05http://www.rapidtables.com/calc/wire/awg-to-mm.htm (AWG converter)

8.2515 mm

53.4751 mm^2

Now, lets say we were using 140 Watt Vmp~17.5 volt panel, and we wanted around 100 Volts Vmp maximum for our MPPT controller:

- 1,200 Watts / 140 Watt per panel = 8.6 panels
- 100 VDC / 17.5 volts = 5.7 panels in series

So, if I wanted 8 panels, I could put:4 in series * 2 parallel strings

9 = 3s*2p

10=5s*2p

Lets do 10 panels (5sx2p) for a 1,400 Watt array (just to show the wire size reduction.

- 5s * 17.5 volts = 87.5 volts
- 140 Watts / 17.5 Vmp = 8 amps Imp per string
- Vmp-array=87.5 volts; Imp-array=16 amps (2x parallel strings)
- 87.5 volts * 0.03 max drop = 2.625 volt drop, 16 amps, and 33 volts--Voltage drop calculator gives:

14 AWG @ 33 feet:Voltage drop:

2.67Voltage drop percentage:

3.05%Voltage at the end:

84.831.6277 mm

2.0809 mm^2

Or for a slightly larger array (and higher working voltage), we can use about 1/26 times less copper wire vs running at a low "17.5 volt" working voltage.

Does this sort of make sense?

If you give us a "real" system design, and we go through the steps--It will make more sense. Just pure "what if" questions get a bit confusing.

-Bill

33✭