over amps on multi branch
if you wire a sine inverter directly into a mains panel,disconnected from grid, and you have multi branch circuits you can have trouble with excess current on the multi branch neutral wire. But you would be ok if you never exceed the amp rating of the breaker even when using 2 different outlets..,yes?? I mean if you never exceed 15 amps then the single neutral wire,12-14 ga. will handle that ,yes??? THis is all providing that the inverter is ok for doing this,ie ground issues etc..
0 · Share on Twitter