# formula for converting AC Kill-a-watt reading over to DC panel wattage?

Urbandialect
Solar Expert Posts:

**107**✭✭✭✭
http://www.lowes.com/pd_322553-15584-4460_0__?storeId=10151&Ntt=kill-a-watt&UserSearch=kill-a-watt&productId=3191393&N=0&catalogId=10051&langId=-1

^ just bought this

Once i get the numbers, how do i convert that over to DC panel wattage? Lets say my Computer is pulling 136 watts (AC) what is that in DC? How many panel watts will I need to cover that? and what about the MSW inverter? http://www.justcardvdplayers.com/vectorvec050c1500-wattpowerinverter.aspx <- this is what i'm using, how much am I loosing in the DC to AC conversion w/the inverter that I will need to factor into the equations?

Thank you

^ just bought this

Once i get the numbers, how do i convert that over to DC panel wattage? Lets say my Computer is pulling 136 watts (AC) what is that in DC? How many panel watts will I need to cover that? and what about the MSW inverter? http://www.justcardvdplayers.com/vectorvec050c1500-wattpowerinverter.aspx <- this is what i'm using, how much am I loosing in the DC to AC conversion w/the inverter that I will need to factor into the equations?

Thank you

#### Categories

- 26K All Categories
- 201 Forum & Website
- 109 Solar Forum News and Announcements
- 1.3K Solar News, Reviews, & Product Announcements
- 154 Solar Information links & sources, event announcements
- 857 Solar Product Reviews & Opinions
- 246 Solar Skeptics, Hype, & Scams Corner
- 20.6K Solar Electric Power, Wind Power & Balance of System
- 3.4K General Solar Power Topics
- 6.3K Solar Beginners Corner
- 922 PV Installers Forum - NEC, Wiring, Installation
- 1.9K Advanced Solar Electric Technical Forum
- 4.9K Off Grid Solar & Battery Systems
- 356 Caravan, Recreational Vehicle, and Marine Power Systems
- 988 Grid Tie and Grid Interactive Systems
- 605 Solar Water Pumping
- 778 Wind Power Generation
- 612 Energy Use & Conservation
- 477 Discussion Forums/Café
- 221 In the Weeds--Member's Choice
- 73 Construction
- 96 New Battery Technologies
- 87 Old Battery Tech Discussions
- 3.8K Solar News - Automatic Feed
- 3.8K Solar Energy News RSS Feed

## Comments

17,615✭✭Direct conversion to panel Watts isn't actually possible. Panels produce power only during sunlight; usage can be any time, and you have to factor in the hours.

But here's the Icarus Formula that can give you a pretty good estimate of over-all conversion:

Panel Watts * hours of good sun / 2 = AC Watt hours.

Otherwise you need the Watt hours the device uses plus the Watt hours the inverter uses factored by the inverter's efficiency divided by the nominal system Voltage to get a rough idea of how many Amp hours you need. Since most batteries should not be discharged below 50% you multiply that by at least 2 to get the minimum battery bank size. That number would be rounded up to the nearest available batteries. The size the battery bank ends up being determines how much PV you need to recharge it. 5% - 13% of the total Amp hour capacity is recommended for the peak current, times the system charging Voltage (according to battery maker's specs) less panel efficiency (which will vary with the particular install site).

Yes, I can make it even more complicated than that! Did I mention wire losses?

30,947adminA 136 watts sounds like a desktop computer... My laptop is around 20-30 watts...

And, it depends on how many hours a day you want to run your computer.

Say you want 10 hours a day, 136 watts average power, and you get 4 hours or better of full sun equivalent per day 9 months of the year.

Assuming average system efficiency of 0.52 (very close to the 1/2 losses):

- 136 watts * 10 hours * 1/0.52 system eff * 1/4 hours of sun = 654 watts of solar panels minimum

And, we recommend 1-3 days of storage, and not to take the battery below 50% state of charge... Assuming 12 volt battery, 85% efficient inverter:- 136 watts * 10 hours * 1/12 volts * 1/0.85 eff * 2 days * 1/0.50 max discharge = 533 AH battery bank

And to double check the ratio of solar panel to battery bank is good (5% to 13% recommended rate of charge)... Use 10% rate of charge and 77% charger+panel derating:- 533 AH * 14.5 volts charging * 1/0.77 derating * 0.10 rate of charge = 1,004 watts...

So, for my mythical system, your recommended panel size would be around 650-1,000 watts or so...-Bill

107✭✭✭✭What the ****? How about I come back w/the Kill a watt numbers tomorrow of the devices i'm trying to run, then we figure it out from there.

107✭✭✭✭Yes, i'm running a desktop, with a surround sound system hooked up to it, haven't got the kill-a-watts reading off it yet, I'm almost finished with my 600 watt array, and you know I have 2 battery banks, 6 6volt amg batteries rated at 200amp hours, and 6 6volt T105s at 225amp hours... but what's shocking to me is that it takes almost 1kw of DC to run and maintain 150 watts of AC.. mindblowing

5,400✭✭✭✭While I think youR 15% conversion is not quite accrete, a 50% is closer.

Consider this, PV will typically only put out ~80 of rated into a battery under ideal, so there is a 20% loss. Add to that, it takes ~120 ah of power to replace 100 ah of draw, so there is another ~20% loss. Add in inverter efficiency, charge controller loses, wiring loses, and bingo, you are near 50%.

On top of that, you haven't even thought about the opportunity loses when the PV is dialed back because the battery is close to full. This could account for another 10-20% depending on battery/PV configuration.

Thees are just a few of the reasons why we always suggest going grid tie if you have the grid available. As we say, off gird PV comes at twice the price, and half the efficiency, leading to power that is 4 times as expensive per useable KWH.

Tony

3,009✭✭✭✭Hahaha Reality begins to sink in. You have no idea how many people think all they have to do is stick a $150.00 panel on the roof and all their energy problems are over.

Living off grid demands a whole different way of thinking/lifestyle. Unless you have extremely deep and full pockets, there is one rule to live by off grid, and that rule consists of three words: Conserve, conserve, conserve! As has been said by others so many times on this form, it's far easier and cheaper to conserve than to waste power. Unfortunately, most of us have been brought up to see excess energy consumption as normal, not recognizing it as waste.

Good luck. It can be done, we did it.

1so without doing the double check part of it, just the math from the first part.

here is how it seems to break down to get a ball park estimate on what to buy batteries and panels to get started based upon ones needs

for 10 hours a day usage of ac watts

and

assuming 85% efficiency inverter

for every 1w ac usage need 4.8w of panels

for every 1w ac used need 4 ah 12v battery

3,738✭✭✭✭You are mistaking power (watts) for energy (kilowatthours). Watts is a RATE of energy use. Kilowatthours are an AMOUNT of energy.

150 watts for 10 hours is 1.5 kilowatthours of energy. That needs to be stored in your battery. A battery that size needs a certain minimum solar array just to charge it. And, as mentioned, there are many losses going into and out of the battery.

btw, if you only use the computer while the sun shines, you can get away with a much smaller system.

Please elaborate... I hope all those batteries are not all connected together... you will ruin all those batteries pretty quickly if they are wired together to make one battery bank.

Even if they are two separate banks, each of those banks is a far from optimal design... especially the AGM batteries. The problem is that parallel batteries are unstable... when charging them it is difficult to get the charging current to divide up evenly among the parallel paths. AGM batteries have lower resistance, so the resistance of the wiring exacerbates the problem, relative to the flooded batteries.

short discussion here: http://www.wind-sun.com/ForumVB/showthread.php?14674

--vtMaps

17,615✭✭Well, no because Watts isn't what you're after; Watt

hoursis. You can't really equate it directly. The batteries provide the power to run the inverter and anything connected to that; the panels recharge the batteries.1 Watt hour AC @ 85% efficiency becomes 1.18 Watt hours DC. The inverter consumes power to make that which may be 6 Watts for a small inverter or 20 Watts for a large one depending on what the total maximum power needs are. Thus small loads on large inverters are very inefficient.

That 1.18 Watt hours on 12 Volts is 0.098 Amp hours. You could call it 1.0 and say you need 4.0 Amp hours @ 12 Volts, relying on 25% DOD. But ... time of use and size of load demand once again comes in to skew the results.

That is another way to end up with a disappointing system: trying to short-cut between AC Watts and PV panel size and/or battery capacity.