Sizing a 24V Deepcycle Battery System for a specific application
ynanperillo
Registered Users Posts: 2 ✭
Hi Everyone,
I have some devices that I need to connect to an OFFGRID Power Source consisting of a;
(1) unit 500w Solar Panel
(1) unit 500w Wind Turbine
(1) unit hybrid charge controller
(1) unit pure sine wave inverter
All the devices must connect to a power strip that is connected to the inverter output.
Here are the Devices that I am going to use along with their DCrating
*antenna  8.5W max consumption, power supply is 24V 0.5A PoE adapter
*camera1  10W, 5V 2 A adapter
*sensor1  216mW, 12V 1A adapter
*sensor2  180mW, 12V 1A adapter
*RTU1  6W, 12V 2A Adapter
*RTU2 4W, 12V 2A Adapter
*IP Phone  12W. 12V 2A Adapter
*Amplifier  200W, connected directly to 220v output of the inverter
BUT I do not know how can I determine the following;
1. AmpereHour size of the (24v) deepcycle battery to be used
2. how many deep cycle batteries I need to use to provide at least 72hours of operation for my devices
I do not know how can I compute for these things given that;
*I only have the DC ratings of my devices, I do not know how long can a FULLCHARGED (24V) Deepcycle battery system provide for the Inverter to produce 220V for 72Hours.
Thank you...
I have some devices that I need to connect to an OFFGRID Power Source consisting of a;
(1) unit 500w Solar Panel
(1) unit 500w Wind Turbine
(1) unit hybrid charge controller
(1) unit pure sine wave inverter
All the devices must connect to a power strip that is connected to the inverter output.
Here are the Devices that I am going to use along with their DCrating
*antenna  8.5W max consumption, power supply is 24V 0.5A PoE adapter
*camera1  10W, 5V 2 A adapter
*sensor1  216mW, 12V 1A adapter
*sensor2  180mW, 12V 1A adapter
*RTU1  6W, 12V 2A Adapter
*RTU2 4W, 12V 2A Adapter
*IP Phone  12W. 12V 2A Adapter
*Amplifier  200W, connected directly to 220v output of the inverter
BUT I do not know how can I determine the following;
1. AmpereHour size of the (24v) deepcycle battery to be used
2. how many deep cycle batteries I need to use to provide at least 72hours of operation for my devices
I do not know how can I compute for these things given that;
*I only have the DC ratings of my devices, I do not know how long can a FULLCHARGED (24V) Deepcycle battery system provide for the Inverter to produce 220V for 72Hours.
Thank you...
Comments

ynanperillo said:I do not know how long can a FULLCHARGED (24V) Deepcycle battery system provide for the Inverter to produce 220V for 72Hours.
The only way to answer the question is know your load... how much DC current does the inverter draw while operating your AC loads.
It is not hard to measure the AC load of your devices... watthour meters are cheap. So measure the AC load of your devices, and tell us the model of your inverter. The inverter will use a certain minimum amount of power and have a certain conversion efficiency. If we know the AC output of the inverter, we can calculate its DC power input and that will be the critical number we need to answer your question.
vtMaps
4 X 235watt Samsung, Midnite ePanel, Outback VFX3524 FM60 & mate, 4 Interstate L16, trimetric, Honda eu2000i 
I guess you are in the Philippines?
For solar power systems, as vtMaps saysIt starts with knowing your loads... Not only Watts or Amps (@ xx Volts), it is how many hours per day you want to run them... 10 Watts * 1 hour per day = 10 Watt*Hours per day
 10 Watts * 24 hours per day = 240 Watt*Hours per day
 1 amp (at 12 volts) * 8 hours per day = 8 AH per day
 8 AH per day * 12 volts = 96 WH per day
In general, you will need to design your loads to conserve as much energy as possible. For example, you have some 12 volt loadsIf they can run from a 12 volt battery (~10.5 to 15.5 VDC). Sometimes, it is better to just put in an AC inverter (stable AC voltage) and isolate the DC loads from the very wide voltage range of a typical DC Solar Battery Bank.
For an AC inverterIf you stay with a 12 VDC battery bank, this MorningStar 300 Watt unit is pretty nice (120 VAC US, 230 VAC for other regions):
http://www.morningstarcorp.com/products/suresine/
That inverter takes ~6 Watts just being "turned on without any AC load"If you have small devices that take a few Watts (or less) loadsPerhaps direct 12 volt connection to battery or smaller 12 volt to 12 volt buck/boost DC converters would be better for those loads and only run the inverter when needed (the Morningstar is nice, has both remote on/off input, and low power "search mode" which may help conserve power). If you have to send energy longer distances, 230 VAC may be a better choice (sending lots of 12 volt current over longer distances can be a huge problem because of voltage drop)..
Bill
Near San Francisco California: 3.5kWatt Grid Tied Solar power system+small backup genset 
vtmaps said:ynanperillo said:I do not know how long can a FULLCHARGED (24V) Deepcycle battery system provide for the Inverter to produce 220V for 72Hours.
The only way to answer the question is know your load... how much DC current does the inverter draw while operating your AC loads.
It is not hard to measure the AC load of your devices... watthour meters are cheap. So measure the AC load of your devices, and tell us the model of your inverter. The inverter will use a certain minimum amount of power and have a certain conversion efficiency. If we know the AC output of the inverter, we can calculate its DC power input and that will be the critical number we need to answer your question.
vtMaps
Hello,
Thanks for the answer!
I attached here the datasheet of the Inverter and charge controller that I will going to use.
Inverter
Charge Controller 
ynanperillo said:Hello,Thanks for the answer!
I attached here the datasheet of the Inverter and charge controller that I will going to use.
The inverter appears to draw 0.7 amps X 24 volts = 16.8 watts. If you turned on the inverter without a load, it would consume 16.8 watts X 24 hours = 0.403 kilowatthours per day. (By the way, my ultraefficient refrigerator draws that much every day).
The inverter has a maximum efficiency of 90%, so if you are drawing 200 AC watts, you are drawing at least 222 watts from the battery. These inverter losses must be added to your load (still to be determined) before you can calculate the size battery you need.
The 'under voltage shutoff' of the inverter is 21.6 volts. That is too low to protect the battery... that shutoff voltage is to protect the inverter, not the battery.
The controller has optional temperature compensation... do you have a remote battery temperature sensor for the controller? Also, the controller is a PWM type... whether it is suitable to your application depends upon the specs of your solar panel (which you have not mentioned). I can't tell from the spec sheet whether the controller has adjustable charging parameters.
vtMaps
4 X 235watt Samsung, Midnite ePanel, Outback VFX3524 FM60 & mate, 4 Interstate L16, trimetric, Honda eu2000i
Categories
 All Categories
 221 Forum & Website
 129 Solar Forum News and Announcements
 1.3K Solar News, Reviews, & Product Announcements
 189 Solar Information links & sources, event announcements
 886 Solar Product Reviews & Opinions
 254 Solar Skeptics, Hype, & Scams Corner
 22.3K Solar Electric Power, Wind Power & Balance of System
 3.5K General Solar Power Topics
 6.7K Solar Beginners Corner
 1K PV Installers Forum  NEC, Wiring, Installation
 2K Advanced Solar Electric Technical Forum
 5.5K Off Grid Solar & Battery Systems
 424 Caravan, Recreational Vehicle, and Marine Power Systems
 1.1K Grid Tie and Grid Interactive Systems
 651 Solar Water Pumping
 815 Wind Power Generation
 621 Energy Use & Conservation
 608 Discussion Forums/Café
 302 In the WeedsMember's Choice
 74 Construction
 124 New Battery Technologies
 108 Old Battery Tech Discussions
 3.8K Solar News  Automatic Feed
 3.8K Solar Energy News RSS Feed