Sizing my battery bank
Options
steelheadguy
Registered Users Posts: 19 ✭✭
I have a greenhouse with 10 dc fans and 4 panels.
The 4 285 watt 24 volt panels are wired in 2 series for 48 volts.
My fans total 8 amps. Correct my math if Im wrong. Im looking for 20 hrs worth of energy stored.
8 amps x 20 hrs = 160 ah x 2 (50% discharge) = 320 amp hours needed at 48 volts.
Is this a correctly sized battery bank?
The 4 285 watt 24 volt panels are wired in 2 series for 48 volts.
My fans total 8 amps. Correct my math if Im wrong. Im looking for 20 hrs worth of energy stored.
8 amps x 20 hrs = 160 ah x 2 (50% discharge) = 320 amp hours needed at 48 volts.
Is this a correctly sized battery bank?
Comments

steelheadguy wrote: »The 4 285 watt 24 volt panels are wired in 2 series for 48 volts.
My fans total 8 amps. Correct my math if Im wrong. Im looking for 20 hrs worth of energy stored.
8 amps x 20 hrs = 160 ah x 2 (50% discharge) = 320 amp hours needed at 48 volts.
Yes, basically correct if you want to run the fans 20 hours straight (no solar/generator/utility power). By the way, is this 10 hours per day with two days of back up power? Or do you run the fans 20 hours out of 24 hours per day? Do you run 9 months a year (no winter)? Or do you run during winter (low amounts of sun)? Where is the system installed (amount of sun by season)?
Charging, lets do some quick rule of thumb checks. First, you want to charge the battery bank at 5% to 13% rate of charge. If this is an "emergency power system", you might get away with a 5% rate of chargeHowever, if this is a daily use system, you probably want a larger array: 320 AH * 59 volts charging * 1/0.77 panel+controller deratings * 0.05 rate of charge = 1,226 Watt array minimum
 320 AH * 59 volts charging * 1/0.77 panel+controller deratings * 0.10 rate of charge = 2,452 Watt array nominal
 320 AH * 59 volts charging * 1/0.77 panel+controller deratings * 0.13 rate of charge = 3,188 Watt array "cost effective" maximum
 8 amps * 48 volts * 10 hours per day * 1/0.61 DC system eff * 1/3.0 hours per day = 2,098 Watt array minimum (10 hours per day operation)
 8 amps * 48 volts * 20 hours per day * 1/0.61 DC system eff * 1/3.0 hours per day = 4,197 Watt array minimum (20 hours per day operation)
 (320 AH * 0.10 rate of charge + 8 amps) * 59 volts charging * 1/0.77 panel+controller derating = 3,065 Watt array minimum (based on 10% rate of charge)
If you run the fans 10 hours per daythen you discharge the battery bank 25% per dayVery common usage for off grid. If you run the fans 20 Hours per day, that is 50% per day dischargeThat can be quite difficult to recharge a lead acid battery bank back in one day... That can easily be 10+ hours per day of charging, and, you may only get 6 hours per day of sun during "nonsummer" operation. If you operated winter/early spring 20 hours per day and want to run fans during cloudy weatherThen you might need to do a 2x larger AH battery bank (or choose another battery chemistry/other way of running ventilation/cut back on cloudy days, etc.).
Bill
Near San Francisco California: 3.5kWatt Grid Tied Solar power system+small backup genset
Categories
 All Categories
 219 Forum & Website
 127 Solar Forum News and Announcements
 1.3K Solar News, Reviews, & Product Announcements
 187 Solar Information links & sources, event announcements
 885 Solar Product Reviews & Opinions
 254 Solar Skeptics, Hype, & Scams Corner
 22.3K Solar Electric Power, Wind Power & Balance of System
 3.5K General Solar Power Topics
 6.7K Solar Beginners Corner
 1K PV Installers Forum  NEC, Wiring, Installation
 2K Advanced Solar Electric Technical Forum
 5.5K Off Grid Solar & Battery Systems
 423 Caravan, Recreational Vehicle, and Marine Power Systems
 1.1K Grid Tie and Grid Interactive Systems
 647 Solar Water Pumping
 814 Wind Power Generation
 621 Energy Use & Conservation
 605 Discussion Forums/Café
 299 In the WeedsMember's Choice
 74 Construction
 124 New Battery Technologies
 108 Old Battery Tech Discussions
 3.8K Solar News  Automatic Feed
 3.8K Solar Energy News RSS Feed