Help with wind and solar hybrid system
Options
ecoconsult
Registered Users Posts: 1
Hello,
I have been charged with the task of trying to figure out how long we can run a compressor on a solar/wind system we are building. We have a 600W wind turbine and an 85W (12V) solar panel charging a bank of 4, 12V batteries (122AH). I know this doesn't sound like enough but it is what we have. How long do you think it would take these to charge the bank of batteries?
We are trying to run a 460W (115V, 4A) air compressor off of it (going though a Whistler Pro2500W 2,500 Watt Power Inverter). I am guessing we won't be able to run it for more than a couple hours a week, if that, but I don't know how to calculate it. I know I need to add in a factor of safety for cloudy/windless days.
We are in Connecticut and are only looking to run this in the summer months.
I am not sure what else to include but hopefully someone can help at least get me started.
Thanks!!!
I have been charged with the task of trying to figure out how long we can run a compressor on a solar/wind system we are building. We have a 600W wind turbine and an 85W (12V) solar panel charging a bank of 4, 12V batteries (122AH). I know this doesn't sound like enough but it is what we have. How long do you think it would take these to charge the bank of batteries?
We are trying to run a 460W (115V, 4A) air compressor off of it (going though a Whistler Pro2500W 2,500 Watt Power Inverter). I am guessing we won't be able to run it for more than a couple hours a week, if that, but I don't know how to calculate it. I know I need to add in a factor of safety for cloudy/windless days.
We are in Connecticut and are only looking to run this in the summer months.
I am not sure what else to include but hopefully someone can help at least get me started.
Thanks!!!
Comments

Welcome to the forum EC!
OK, down to specifics... Is that 4x 122 AH batteries, or a 122 AH @ 12 volt battery bank?
Next, how have you measured the air compressor's power usage... With induction motors, there can be a fairly large difference between Watts and VA.... Real quick, with AC voltage, there is a "phase shift" between the voltage and the currentOne way to write the power equations is:
Power = Voltage * Current == Accurate for DC Circuits
Power = Voltage * Current * Power Factor = Voltage * Current * Cos (voltage to current phase angle)
VA rating = Voltage * Current (used for planning wire sizes, fuses/breakers, inverter & generator sizing)
Cos (angle) and PF range from 0.0 to 1.0 with 0.0 being no power being used to 1.0 being AC power is used "perfectly". Induction motors typically run around 0.6 to 0.8 Power Factor.
If you can, get a KillaWatt type meter and measure the Volts, Amps, PF, and kWH per day used.
SoUsing some assumptions (you can plug in your own numbers if I am wrong): 4x 12 volt @ 122 AH batteries in parallel = 12 volt @ 488 AH battery bank
 Compressor is VA=115v * 4 amps = 460 VA
 Compressor is Watts = 115 V * 4 amps * 0.8 PF = 368 Watts
 85 Watt solar panel
 600 Watt turbine
Assuming the battery bank is going to supply most of the power (i.e., no sun, no wind, worst case). Normally, would recommend daily cycling of 25% to 50% of battery capacity... Going down often below 50% will make battery life shorter (maybe a few hundred cycles for a deep cycle battery), and going below 20% state of charge will probably "kill" the battery bank. 12 volts * 488 AH * 0.50 max typical discharge * 1/(460 VA * 0.8 pf) * 0.85 inverter efficiency = 3.98 hours
 12 volts * 400 AH * 0.50 max typical discharge * 1/(460 VA * 0.8 pf) * 0.85 inverter efficiency = 3.3 hours
Month
Solar Radiation
(kWh/m^{2}/day)
1
2.92
2
3.79
3
4.34
4
5.17
5
5.33
6
5.86
7
5.67
8
5.39
9
4.72
10
3.71
11
2.65
12
2.37
Year
4.33
Call it ~5.0 hours of sun minimum for summer. The energy collected would be: 85 watts * 0.52 typical end to end solar system efficiency * 5.0 hours of sun per day = 221 Watt*Hours per day (long term average)
221 WH per day / (460 VA * 0.8 PF) = 0.60 hours per day
NowSome other design issues... For a battery bank, you should have between 5% and 13% rate of charge... And if you want to cycle the battery bank daily, you should probably look at 10% or more rate of charge: 488 AH * 14.5 volts charging * 1/0.77 panel+controller derating * 0.05 rate of charge = 459 Watt array minimum
 488 AH * 14.5 volts charging * 1/0.77 panel+controller derating * 0.10 rate of charge = 919 Watt array nominal
 488 AH * 14.5 volts charging * 1/0.77 panel+controller derating * 0.13 rate of charge = 1,195 Watt array "cost effective" maximum
If your battery bank is really 122 AH, then we need to look at some other issues (i.e., the battery bank is really not large enough to power a 460 Watt compressor).
I personally have not seen/read about very many small wind systems that generate much in the way of useful energy... If you have measured output over time (summer use), then we can take that into account.
Hope this helps.
BillNear San Francisco California: 3.5kWatt Grid Tied Solar power system+small backup genset
Categories
 All Categories
 219 Forum & Website
 127 Solar Forum News and Announcements
 1.3K Solar News, Reviews, & Product Announcements
 187 Solar Information links & sources, event announcements
 885 Solar Product Reviews & Opinions
 254 Solar Skeptics, Hype, & Scams Corner
 22.3K Solar Electric Power, Wind Power & Balance of System
 3.5K General Solar Power Topics
 6.7K Solar Beginners Corner
 1K PV Installers Forum  NEC, Wiring, Installation
 2K Advanced Solar Electric Technical Forum
 5.5K Off Grid Solar & Battery Systems
 422 Caravan, Recreational Vehicle, and Marine Power Systems
 1.1K Grid Tie and Grid Interactive Systems
 647 Solar Water Pumping
 814 Wind Power Generation
 621 Energy Use & Conservation
 604 Discussion Forums/Café
 299 In the WeedsMember's Choice
 74 Construction
 124 New Battery Technologies
 107 Old Battery Tech Discussions
 3.8K Solar News  Automatic Feed
 3.8K Solar Energy News RSS Feed