Ralph Day wrote: »
Do you have automatic or manual louvres to stop reverse convection cooling at night? I imagine there would be a flow of cold air out the bottom if not.
dwh wrote: »
Overall, pretty good. Nice balance between the 50% discharge rule on the battery and the ability to recharge it from 410w of PV. For the cold though I think you should be okay adding another battery without upgrading the PV.
I wouldn't trust that Power Jack half as far as I could throw it. Besides almost certainly being a blatant violation of your electric utility's terms of service, that company makes cheap (and dangerous) crap:
(Yes, I know that page is about a different inverter. But it's from the same company.)
Plug-in grid-tie inverters are a new phenomena, so they haven't yet been addressed by the powers that be. If I were a betting man I would put my money on that sort of gadget being explicitly outlawed in the not too distant future.
InVenture wrote: »
* Grid-Tie?? This is not a grid-tie system.
edraket wrote: »
hello, i am new to this site, and have a lot of reading to do.
I am from Belgium, and would like to share my website about our PV-installation:
Timothy wrote: »
Hy all,here is my blog Diy Solar Panels,its about...well solar panels with a section for wind energy(but im currently looking for reference on that so hooping i can find some tips here)
Stop by,check it out,give me some pointers on it,i will appreciate it.