# 3-phase AC current measurements with clamps

lazza
Solar Expert Posts:

**334**✭✭✭
Hi,

We're about to put in an Efergy E2 energy monitor for a house that has 3 phase electricity. The system is with a neutral, hence a Wye system, so each phase gives 230V between it and the neutral wire.. can I therefore simply put one clamp around the neutral wire to measure the total power consumption?

We're about to put in an Efergy E2 energy monitor for a house that has 3 phase electricity. The system is with a neutral, hence a Wye system, so each phase gives 230V between it and the neutral wire.. can I therefore simply put one clamp around the neutral wire to measure the total power consumption?

#### Categories

- 26.2K All Categories
- 202 Forum & Website
- 110 Solar Forum News and Announcements
- 1.3K Solar News, Reviews, & Product Announcements
- 157 Solar Information links & sources, event announcements
- 862 Solar Product Reviews & Opinions
- 248 Solar Skeptics, Hype, & Scams Corner
- 20.8K Solar Electric Power, Wind Power & Balance of System
- 3.4K General Solar Power Topics
- 6.3K Solar Beginners Corner
- 933 PV Installers Forum - NEC, Wiring, Installation
- 1.9K Advanced Solar Electric Technical Forum
- 4.9K Off Grid Solar & Battery Systems
- 362 Caravan, Recreational Vehicle, and Marine Power Systems
- 991 Grid Tie and Grid Interactive Systems
- 607 Solar Water Pumping
- 781 Wind Power Generation
- 612 Energy Use & Conservation
- 493 Discussion Forums/Café
- 229 In the Weeds--Member's Choice
- 77 Construction
- 96 New Battery Technologies
- 91 Old Battery Tech Discussions
- 3.8K Solar News - Automatic Feed
- 3.8K Solar Energy News RSS Feed

## Comments

31,143adminNo--You cannot.

The neutral wire carries the difference of the A/B/C three phase legs...

If you run 10 Amps A to Neutral => 10 amps on Neutral

If you run 10 amps on A+B+C then neutral would have (ideally) zero amps.

Its Vector Math, so the additions are not simple (if you have 10 amps on all three A-N with 1.0 PF and B-N with 0.5 PF and C-N with 0.67 PF, you will have some sort of non-zero current on the Neutral).

However--I do have a question... In the US, we use Delta and Wye (or "Y" or "Star") transformers from the utility (each has their own advantages/problems).

In the US we us Phase to Neutral (120 VAC) and Phase to Phase (240 VAC for Delta, 208 VAC for Wye).... And higher voltages too.

Are you using both Phase to Neural and Phase to Phase for this installation--Or just Phase to Phase (and no neutral needed)? Or only Phase to Neutral? (I don't know how the standard residential grid power is wired in Europe/Spain).

-Bill

1,973✭✭✭No. If the source/load is balanced, the current in the neutral will be zero. If not the neutral will carry only the difference between the unbalanced phases. You've got to monitor all three phases for a building that has some balanced loads and some single phase loads.

3,123✭✭✭✭As stated, you cannot even measure the total current that way, let alone the total energy. By knowing both the current in each phase and at the same time the voltage on each phase (so that you can detect the phase relationship between the current and the voltage) you can measure the power flowing in or out.

If all of the loads are purely resistive, you can calculate the power knowing only the magnitude of the currents and voltages.