# converting C/8 to C/20 rate

westbranch
Solar Expert Posts:

**5,175**✭✭✭✭
I am looking into some newer AGMs. The only rate I can find in Exide's literature is the C/8 rate, but I would like to translate that number to C/20 for comparison to my old battery.

the battery is an Absolyte GX 2000 C/8 is 2000Ah @ 1.75 V @ 25* C

http://www.ieeco.net/Documents/Batteries/ExideAbsolyteGX.pdf page 3

they also provide 24 hr, 12 Hr , 10 hr and 8 hr discharge data @ 1.75 V @ 25* C as follows:

Time....24hr ...... 12hr ...... 10hr ..... 8hr

Amps ...96 ........ 178 ........208 .......250

then a qualifier, bottom page 5,

"Note: To obtain amps for each GX system — multiply the amps/positive value from

table by the number of positive plates "

System .............. GX2000 GX3000 GX4000 GX5000 GX6000

# of Positive Plates 12 .........18 .......24 .......30 ..... 36

This last part makes no sense to me as 8hr x 250A = 2000Ah, and 12 hr x 178A = 2136 Ah and 24 hr x 96 = 2304 yet

96A x 12 ( from table) = 1152A

???Am I correct in saying the (C/20) Ahr rating for the GX2000 is ~ =2248Ahr??

the battery is an Absolyte GX 2000 C/8 is 2000Ah @ 1.75 V @ 25* C

http://www.ieeco.net/Documents/Batteries/ExideAbsolyteGX.pdf page 3

they also provide 24 hr, 12 Hr , 10 hr and 8 hr discharge data @ 1.75 V @ 25* C as follows:

Time....24hr ...... 12hr ...... 10hr ..... 8hr

Amps ...96 ........ 178 ........208 .......250

then a qualifier, bottom page 5,

"Note: To obtain amps for each GX system — multiply the amps/positive value from

table by the number of positive plates "

System .............. GX2000 GX3000 GX4000 GX5000 GX6000

# of Positive Plates 12 .........18 .......24 .......30 ..... 36

This last part makes no sense to me as 8hr x 250A = 2000Ah, and 12 hr x 178A = 2136 Ah and 24 hr x 96 = 2304 yet

96A x 12 ( from table) = 1152A

???Am I correct in saying the (C/20) Ahr rating for the GX2000 is ~ =2248Ahr??

KID #51B 4s 140W to 24V 900Ah C&D AGM

CL#29032 FW 2126/ 2073/ 2133 175A E-Panel WBjr, 3 x 4s 140W to 24V 900Ah C&D AGM

Cotek ST1500W 24V Inverter,OmniCharge 3024,

2 x Cisco WRT54GL i/c DD-WRT Rtr & Bridge,

Eu3/2/1000i Gens, 1680W & E-Panel/WBjr to come, CL #647 asleep

West Chilcotin, BC, Canada

#### Howdy, Stranger!

It looks like you're new here. If you want to get involved, click one of these buttons!

## Quick Links

#### Categories

- 25.3K All Categories
- 195 Forum & Website
- 103 Solar Forum News and Announcements
- 1.2K Solar News, Reviews, & Product Announcements
- 145 Solar Information links & sources, event announcements
- 840 Solar Product Reviews & Opinions
- 246 Solar Skeptics, Hype, & Scams Corner
- 20K Solar Electric Power, Wind Power & Balance of System
- 3.3K General Solar Power Topics
- 6.1K Solar Beginners Corner
- 889 PV Installers Forum - NEC, Wiring, Installation
- 1.8K Advanced Solar Electric Technical Forum
- 4.7K Off Grid Solar & Battery Systems
- 325 Caravan, Recreational Vehicle, and Marine Power Systems
- 961 Grid Tie and Grid Interactive Systems
- 582 Solar Water Pumping
- 751 Wind Power Generation
- 608 Energy Use & Conservation
- 375 Discussion Forums/Café
- 167 In the Weeds--Member's Choice
- 58 Construction
- 75 New Battery Technologies
- 75 Old Battery Tech Discussions
- 3.8K Solar News - Automatic Feed
- 3.8K Solar Energy News RSS Feed

## Comments

3,738✭✭✭✭Westbranch, If you use the charts, just multiply the amps by the hours to get amphours.

If you use the graphs, the numbers shown are per plate and you would need to multiply them by 12 (for the gx2000) to get something that makes sense.

For example, the graph on the bottom of page 6:

The 8 hour line intersects the 1.75 volt/cell line at about 167 amphours per positive plate. 12 plates X 167 amphour per plate = 2000 amphours

--vtMaps

5,175✭✭✭✭Thanks VT, I was doing things right then. I just am not sure of how to interpolate between 12 and 24 hr rates.

The 2248Ah is straight line interpolation, which I know is close...

KID #51B 4s 140W to 24V 900Ah C&D AGM

CL#29032 FW 2126/ 2073/ 2133 175A E-Panel WBjr, 3 x 4s 140W to 24V 900Ah C&D AGM

Cotek ST1500W 24V Inverter,OmniCharge 3024,

2 x Cisco WRT54GL i/c DD-WRT Rtr & Bridge,

Eu3/2/1000i Gens, 1680W & E-Panel/WBjr to come, CL #647 asleep

West Chilcotin, BC, Canada