But I really did not buy big enough for any added loads. I am charging through the inverter, and if a load comes on it really bogs the generator down, this cannot be good.
Wondering if I should purchase a 24 volt charger and charge the battery directly with that ? Then any loads that popped up would be isolated from the generator
Anyone doing this?
Off grid, all solar, passive and active ( winter wood heat supplements) solar DHW, no backup.
Array 1 1980w, 12 Solarworld 165 w panels - Outback Flex max 80
Array 2 1590 w, 6 Solarworld 265 w panels - Outback flex max 60
Well array 600w, 6 Kyocera 130 w with Grundfos sqflex11 and cu200 to elevated storage, ( 2- 330 g tanks,) no battery storage at well
GB industrial 510 AH battery 24 V
Outback VFX 3525 inverter,