Placement of Automatic Transfer Switch for Grid-Tied Battery Back up System
I would like to place a generator with an ATS on my Grid-Tied Battery Back up System. I have an Eaton EGSU100ACA ATS. I made a outline of my system (see pdf file). I wanted to get advice on the placement of the ATS. The most logical place that comes to mind is the AC line coming from the outside main utility panel to the midnite solar E-panel. Would this be appropriate placement?