Re: Wiring Diagram Needed for SquareD QO Breaker Box
I used a QO box and breakers. It is pretty simple. Assuming it is a split phase panel, you can wire a jumper between the two hot buss lugs, if you choose not to use a main breaker. Then you bring the positive from the battery to one of the lugs. (fused at the battery as well). If you choose to use w main breaker, you can jump between both lugs of the main to energize the busses. Then install what ever branch circuits as desired, properly sized and wired. Energize the Breakers with the positive. Then return the negs to the neutral buss, while attaching the home run to the neutral lug on that buss, returning to the battery neg.
Hope this helps,
Ps I would lable every end of every positive with red tape so that you don't get confused ns accidentally short a positive to a negative.
Please note, being a moderator does not add any weight to my opinions 300 watts Siemens/BP panels,plus a Sun 90,, making ~400. ~30 amps into Rogue MPT-3024, 450 ah of Trojan T-105, Morningstar ts300 inverter, a Tri-Metric meter.a collection of antique generators, plus 2 Honda eu-1000i's (also a BS2512 IX controller) and assorted other stuff!