Off Grid Solar & Battery Systems
charging battery bank with generator
Do you have the inverter hooked up to a panel wired split phase and use any 240v loads? Or are your loads 120V, trying to get a picture of what it is you have, a solution such as
suggested using a smaller inverter during periods of low demand, at night for example would dramatically reduce the taxing of the batteries by shifting the 24 hour loads to it. How are you determining the DOD of the battery? Again, just curious.
1500W, 6× Schutten 250W Poly panels , Schneider 150 60 CC, Schneider SW 2524 inverter, 8×T105 GC 24V nominal